*   BUILDING DESCRIPTIONS FILE TRNSYS
*   FOR BUILDING: IOWAB.BUI
*   GET BY WORKING WITH TUD-Bid

* PROJECT
*+++ PROJECT
*+++ TITLE=undefined
*+++ DESCRIPTION=undefined
*+++ CREATED=undefined
*+++ ADDRESS=undefined
*+++ CITY=undefined
*+++ SWITCH=undefined

* COMMENTS
* BUILDING DESCRIPTIONS FILE OF EMPA test cell
* GET BY SIMULATION

PROPERTIES
 DENSITY =1.204
 CAPACITY =1.012
 HVAPOR =2454
 SIGMA =2.0411E-07
 RTEMP =293.15

TYPES

*------------------LAYERS--------------------------------------------

LAYER SheetSteel
 CONDUCTIVITY = 193.032
 CAPACITY  = 0.4608 : DENSITY = 7837.

LAYER PUfoam
* CONDUCTIVITY = 0.08346 ! temperaturabhaengig aus Test2
 CONDUCTIVITY = 0.080388 ! fuer 22.78C berechnet
 CAPACITY  = 1.800 : DENSITY = 30.

LAYER PUfoamH
 CONDUCTIVITY = 0.252
 CAPACITY  = 1.800 : DENSITY = 45.

LAYER Plywood
* CONDUCTIVITY = 0.50917  ! temperaturabhaengig
 CONDUCTIVITY = 0.50184  ! fuer 17.49C berechnet
 CAPACITY  = 1.605 : DENSITY = 850.

LAYER EPSfoam
* CONDUCTIVITY = 0.134075 ! temperaturabhaengig
 CONDUCTIVITY = 0.128808 ! fuer 17.49C berechnet
 CAPACITY  = 1.460 : DENSITY = 28.

LAYER Cldbrdg
* 16.4376 gesamt=0.144 external+16.2936 chamber
* CONDUCTIVITY = 16.4376
* CAPACITY  = 0.1 : DENSITY = 1.
RESISTANCE=0.060836

*------------------INPUTS---------------------------------------------
INPUTS CellTemp FanPower
INPUTS TsoFloor TSOCeil TSOWest TSONorth TSOEast
INPUTS Hfront HfrontC HfrontF HfrontSW HfrontSG HbackSW HbackSG
INPUTS Eshade CbrExTemp CbrGuTemp

*------------------WALLS----------------------------------------------

WALL Ceiling
 LAYERS = SheetSteel PUfoam SheetSteel
 THICKNESS= 0.0007 0.139 0.0007
 ABS-FRONT = 0.76 : ABS-BACK = 0.76
 RFRONT = 0.92 : RBACK = 0.92
 HFRONT = INPUT 3.6*HfrontC : HBACK = 999.

WALL Floor
 LAYERS = SheetSteel PUfoamH PUfoam SheetSteel
 THICKNESS= 0.0025 0.020 0.140 0.0007
 ABS-FRONT = 0.25 : ABS-BACK = 0.25
 RFRONT = 0.96 : RBACK = 0.96
 HFRONT = INPUT 3.6*HfrontF : HBACK = 999.

WALL Southwall
 LAYERS = Plywood EPSfoam Plywood
 THICKNESS= 0.010 0.130 0.010
 ABS-FRONT = 0.77 : ABS-BACK = 0.77
 RFRONT = 0.93 : RBACK = 0.93
 HFRONT = INPUT 3.6*HfrontSW : HBACK = INPUT 3.6*HbackSW

WALL NEWwall  !North East West walls
 LAYERS = SheetSteel PUfoam SheetSteel
 THICKNESS= 0.0007 0.139 0.0007
 ABS-FRONT = 0.76 : ABS-BACK = 0.76
 RFRONT = 0.92 : RBACK = 0.92
 HFRONT = INPUT 3.6*Hfront : HBACK = 999.

WALL Cbrwall
 LAYERS = Cldbrdg
 THICKNESS= 1.
 ABS-FRONT = 0.6 : ABS-BACK = 0.6
 HFRONT = 999. : HBACK = 999.
*------------------WINDOWS--------------------------------------------
WINDOW Southwindow
 WINID=1
 HINSIDE=  INPUT 3.6*HfrontSG  : HOUTSIDE=  INPUT 3.6*HbackSG  :
 SLOPE=   90.000  : FFRAME=    0.1637 : UFRAME=  6.229 : ABSFRAME=0.25
 RISHADE=  0.0000 : RESHADE=   0.0000 :
 REFLISHADE=  0.0000 : REFLOSHADE=0.  : CCISHADE= 0.0000

*------------------VENTIILATION---------------------------------------
VENTILATION CldbrdgEx
 TEMPERATURE=INPUT 1*CbrExTemp
 AIRCHANGE=0.0038
 HUMIDITY=0

VENTILATION CldbrdgGu
 TEMPERATURE=INPUT 1*CbrGuTemp
 AIRCHANGE=0.4288
 HUMIDITY=0

*HEATING
HEATING CellLoadH
ON=INPUT CellTemp
POWER=1000000
HUMIDITY=0
RRAD=0

*COOLING
COOLING CellLoadC
ON=INPUT CellTemp
POWER=1000000
HUMIDITY=0

*GAIN
GAIN Fan
CONVECTIVE=INPUT 3.6*FanPower
RADIATIVE=0.
HUMIDITY=0.


*INFILTRATION
INFILTRATION Cldbrdg
 AIRCHANGE=0.4326

*---------------------------------------------------------------------
*ORIENTATIONS
ORIENTATION South

ZONES TestCell

*---------------------------------------------------------------------

BUILDING

ZONE TestCell
**South wall
WALL  = Southwall : AREA= 4.7394 : EXTERNAL: ORIENTATION=South : FSKY=0.5
**South window
WINDOW=Southwindow : AREA=1.9866 : ORIENTATION=South : ESHADE=INPUT Eshade :
                                                     FSKY=0.5
**West wall
WALL   = NEWwall : AREA= 10.917: BOUNDARY= INPUT TSOWest : COUPLING= 0
**North wall
WALL   = NEWwall : AREA= 6.726 : BOUNDARY= INPUT TSONorth : COUPLING= 0
**East wall
WALL   = NEWwall : AREA= 10.917: BOUNDARY= INPUT TSOEast : COUPLING= 0
**FUSSBODEN
Floor  = Floor : AREA= 13.184   : BOUNDARY= INPUT TsoFloor : COUPLING= 0
**DECKE
Ceiling= Ceiling : AREA= 13.184: BOUNDARY= INPUT TSOCeil : COUPLING= 0
REGIME
 LWRMODE=2
* INFILTRATION=Cldbrdg
 VENTILATION=CldbrdgEx
 VENTILATION=CldbrdgGu
 GAIN=Fan : SCALE=1.
 HEATING=CellLoadH
 COOLING=CellLoadC
 CAPACITANCE = 350. : VOLUME = 31.114
 TINITIAL =29 : PHIINITIAL =50.0
 WCAPR =1.

OUTPUTS
 TRANSFER : TIMEBASE =0.05
 ZONES = TestCell
 NTYPES= 1 2 25 3 14 16 17 18 19 20 12 61 50 51
END
