$ Yearly simulation using DOE2 for ERS at Ankeny, Iowa
$ Schedules used are the typical offfice building during a year
$ Room B use daylighting (DAYLIGHTING = YES)
$ Comparison for ERH vs HRH
$ Air flow rate with ERH (250,400 CFM) (450,1000 CFM)
$ Fan is on CYCLE-ON-ANY mode
$ Temperature is controlled

$*********************************************************************************
$                    		INPUT FOR ERS LOAD                                 *
$*********************************************************************************
INPUT LOADS		INPUT-UNITS = ENGLISH	OUTPUT-UNITS = METRIC ..

TITLE			LINE-1 *ERS YEARLY ENERGY SIMULATION* ..

ABORT			IF ERRORS ..

DIAGNOSTIC		WARNINGS	CAUTIONS ..

RUN-PERIOD		JUN 4 2006 THRU JUN 10 2006 ..

$****************************** BUILDING DESCRIPTION *****************************
BUILDING-LOCATION	LATITUDE = 41.71		LONGITUDE = 93.61
			ALTITUDE = 	945		AZIMUTH = 0.0	
			TIME-ZONE = 6		DAYLIGHT-SAVINGS = NO
			HOLIDAY = NO ..
			$GROUND-T (90,90,90,90,90,90,100,90,90,90,90,90)..


$********************** SCHEDULES FOR TEST ROOMS *********************************
$*** PEOPLE ***********
PEOPLE-SCH		= SCHEDULE THRU DEC 31	(ALL)(1,24)(1) ..
$*** EQUIPMENT ********
EQP-SCH-A		= SCHEDULE THRU DEC 31 (ALL)	(1,24)(1) ..

EQP-SCH-B		= SCHEDULE THRU DEC 31 (ALL)	(1,24)(0) ..

EQP-SCH			= SCHEDULE THRU DEC 31 (ALL)	(1,24)(0) ..

$*** LIGHTING *********
LIGHT-SCH		= SCHEDULE THRU DEC 31
				(ALL)	(1,4)(0) (5,21)(1) (22,24)(0)..

$****WINDOW SHADING SCHEDULES

SHADE-SCH-DAYLIGHT	=	SCHEDULE THRU DEC 31 (ALL)(1,24)(1) ..
TVIS-NYSAN-SCH     	= 	SCHEDULE THRU DEC 31 (ALL)(1,24)(0.305) ..

TSOL-NYSAN-SCH     	= 	SCHEDULE THRU DEC 31 (ALL)(1,24)(0.325) ..



COND-NYSAN-SCH		=	SCHEDULE THRU DEC 31 (ALL)(1,24)(0.7422) ..

TVIS-MUSLIN-SCH     	= 	SCHEDULE THRU DEC 31 (ALL)(1,24)(0.388) ..

TSOL-MUSLIN-SCH     	= 	SCHEDULE THRU DEC 31 (ALL)(1,24)(0.385) ..


$********************** SCHEDULES FOR OTHER ROOMS *********************************
ZERO-SCH		= SCHEDULE THRU DEC 31 (ALL) (1,24)(0) ..
PEOPLE-STANDARD	= SCHEDULE THRU DEC 31 (ALL) (1,24)(1) ..
LIGHT-STANDARD	= SCHEDULE THRU DEC 31 (ALL) (1,7)(0.0) (8,18)(1) 
							     (19,24)(0.0) ..
EQP-STANDARD	= SCHEDULE THRU DEC 31 (ALL) (1,7)(0) (8,18)(1) (19,24)(0) ..


$***************************** MATERIAL DEFINITION ********************************
$** THIS MATERIAL DEFINITION FOR MATERIAL THAT IS NOT AVAILABLE IN DOE2 DATABASE **
GL1			= MATERIAL
				THICKNESS = 0.0208	CONDUCTIVITY = 0.797
				DENSITY = 138.5		SPECIFIC-HEAT = 0.178 ..



$***************************** GLASS TYPES ****************************************
LOW-E2 		= GLASS-TYPE
			  GLASS-TYPE-CODE = 2001
			  FRAME-ABS = 0.7
			  FRAME-CONDUCTANCE = 3.037
			  SPACER-TYPE-CODE = 1 ..

LOW-E3	 	= GLASS-TYPE
			  GLASS-TYPE-CODE = 2000
			  FRAME-ABS = 0.7
			  FRAME-CONDUCTANCE = 3.037
			  SPACER-TYPE-CODE = 1 ..

CLEAR	 	= GLASS-TYPE
			  GLASS-TYPE-CODE = 2002
			  FRAME-ABS = 0.7
			  FRAME-CONDUCTANCE = 3.037
			  SPACER-TYPE-CODE = 1 ..

WINDOW-TYPICAL	= GLASS-TYPE
				SHADING-COEF = 0.31	GLASS-CONDUCTANCE = 0.30
				PANES = 2 ..

WINDOW-SKYLITE	= GLASS-TYPE
				SHADING-COEF = 0.35	GLASS-CONDUCTANCE = 0.24
				PANES = 1 ..

$***************************** LAYERS DEFININTION **********************************
SET-DEFAULT FOR LAYERS 		INSIDE-FILM-RES = 0.738 .. $0.68 ..  FOR EXTERIOR WALLS & ROOFS

$** ROOF FOR BUILDING EXCEPT THE CLASS ROOMS **
LAY-ROOF		= LAYERS 	MATERIAL = (RG02,AR02,IN47,BP01,CC02,AL23,CC02) ..	

$** ROOF FOR CLASS ROOM **
LAY-CLASS-ROOF	= LAYERS	MATERIAL = (RG02,AR02,IN47,AS01) ..

$** BOTTOM WALL FOR TEST ROOMS **
LAY-TESTWALL-B	= LAYERS	MATERIAL = (CC03,IN42,IN43,AL11,BP01,GP02) ..

$** TOP WALL FOR TEST ROOMS **
LAY-TESTWALL-T	= LAYERS	MATERIAL = (CC04,IN43,AL11,GP02) ..

$** SPANDREL WALL **
LAY-SPAND-WALL	= LAYERS 	MATERIAL = (GL1,AL11,GL1,AL31,IN43,IN13,BP01,GP02) ..

$** OVERHEAD WALL **
LAY-OVH-WALL	= LAYERS	MATERIAL = (CC04,IN43,AL11,IN13) ..

$** CLASS ROOMS WALL **
LAY-CLASS-WALL	= LAYERS	MATERIAL = (CC04,IN43,AL21,IN13,BP01,GP03) ..

$** BOTTOM WALL FOR BUILDING **
LAY-WALL-B		= LAYERS	MATERIAL = (CC03,IN43,AL11,IN13,BP01,GP02) ..

$** TOP WALL FOR BUILDING **
LAY-WALL-T		= LAYERS	MATERIAL = (CC03,IN43,AL11,IN13,GP02) ..

$** INTERIOR WALL
LAY-INT-WALL	= LAYERS 	MATERIAL = (GP02,IN13,GP02) ..

$** CEILING **
LAY-CEILING		= LAYERS 	MATERIAL = (AC03) I-F-R = 0.965 ..

$** GROUND FLOOR **
LAY-FLOOR		= LAYERS	MATERIAL = (CC03,CP02)	I-F-R = 0.5678 ..


$*** CONSTRUCTIONS DEFINITION FOR ROOF, WALL, CEILING, PARTITION, FLOOR, WINDOW AND DOOR *****

$** ROOF FOR BUILDING EXCEPT CLASS ROOM **
ROOF-STD		= CONSTRUCTION
				LAYERS = LAY-ROOF	
				ABSORPTANCE = 0.29	ROUGHNESS = 1 ..

$** ROOF FOR CLASS ROOM **
ROOF-CLASS		= CONSTRUCTION LIKE ROOF-STD	
				LAYERS = LAY-CLASS-ROOF ..

$** TEST ROOM BOTTOM WALL **
WALL-TESTROOM-B	= CONSTRUCTION
				LAYERS = LAY-TESTWALL-B
				ABSORPTANCE = 0.69	ROUGHNESS = 3	 ..

$** TEST ROOM TOP WALL **
WALL-TESTROOM-T	= CONSTRUCTION LIKE WALL-TESTROOM-B		
				LAYERS = LAY-TESTWALL-T ..

$** SPANDRELL WALL **
WALL-SPANDRELL	= CONSTRUCTION
				LAYERS = LAY-SPAND-WALL
				ABSORPTANCE = 0.90	ROUGHNESS = 6 ..

$** OVERHEAD WALL **
WALL-OVERHEAD	= CONSTRUCTION LIKE WALL-TESTROOM-B
				LAYERS = LAY-OVH-WALL ..

$** CLASSROOM WALL **
WALL-CLASSROOM	= CONSTRUCTION LIKE WALL-TESTROOM-B
				LAYERS = LAY-CLASS-WALL ..

$** TYPICAL BUILDING BOTTOM-WALL **
WALL-BOTTOM		= CONSTRUCTION LIKE WALL-TESTROOM-B
				LAYERS = LAY-WALL-B ..

$** TYPICAL BUILDING TOP-WALL **
WALL-TOP		= CONSTRUCTION LIKE WALL-TESTROOM-B
				LAYERS = LAY-WALL-T ..

$** INTERIOR WALL FOR SPACE "INTERIOR-WALL" **
INT-WALL		= CONSTRUCTION		LAYERS = LAY-INT-WALL ..

$** INTERIOR WALL FOR INTERIOR ROOMS
WALL-INT	 	= CONSTRUCTION		U = 0.6 ..

$** CEILING **
CEILING		= CONSTRUCTION		LAYERS = LAY-CEILING ..

$** GROUND FLOOR **
GND-FLOOR		= CONSTRUCTION		LAYERS = LAY-FLOOR ..


$****************** SET DEFAULT VALUES ******************************
SET-DEFAULT FOR WINDOW		X = 0	Y = 3	WIDTH = 14	 HEIGHT = 5 ..

SET-DEFAULT FOR ROOF		CONSTRUCTION = ROOF-STD	Z = 14	
					AZIMUTH = 180	TILT = 0	G-R = 0 ..

SET-DEFAULT FOR UNDERGROUND-FLOOR
					CONSTRUCTION = GND-FLOOR
					U-EFF = 0.05	TILT = 180 ..

SET-DEFAULT FOR INTERIOR-WALL
					CONSTRUCTION = INT-WALL		TILT = 90 ..

SET-DEFAULT FOR SPACE		AREA = 275 ..


$******************* SPACE CONDITIONS **********************************
$** SPACE CONDITION FOR TEST ROOM **

TEST-ROOM-A		= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (72)
				PEOPLE-SCHEDULE		= PEOPLE-SCH
				AREA/PERSON			= 100
				PEOPLE-HG-LAT		= 205
				PEOPLE-HG-SENS		= 245
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-RV 
				LIGHT-TO-SPACE		= 0.8  $ 1
				LIGHTING-KW			= 0.5
				LIGHT-RAD-FRAC		= (0)
				EQUIP-SCHEDULE		= EQP-SCH
				EQUIPMENT-KW		= 1
				FLOOR-WEIGHT		= 0 ..

TEST-ROOM-WA	= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (72)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-RV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.362
				DAYLIGHTING			= YES
				LIGHT-REF-POINT1		= (9.333,51.25,2.375)
				LIGHT-SET-POINT1		= 60 	
				ZONE-FRACTION1		= 1.0
				LIGHT-CTRL-TYPE1		= CONTINUOUS/OFF
				MIN-LIGHT-FRAC    	= 0.03655493
				MIN-POWER-FRAC		= 0.240055249
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				PEOPLE-SCHEDULE		= PEOPLE-SCH
				NUMBER-OF-PEOPLE		= 2 
				PEOPLE-HG-SENS		= 1732.075 ..

TEST-ROOM-WB	= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (72)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-RV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.348
				DAYLIGHTING			= YES
				LIGHT-REF-POINT1		= (9.33,35.75,2.375)
				LIGHT-SET-POINT1		= 60 	
				ZONE-FRACTION1		= 1.0
				LIGHT-CTRL-TYPE1		= CONTINUOUS/OFF
				MIN-LIGHT-FRAC    	= 0.03655493
				MIN-POWER-FRAC		= 0.240055249
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				PEOPLE-SCHEDULE		= PEOPLE-SCH
				NUMBER-OF-PEOPLE		= 2 
				PEOPLE-HG-SENS		= 1732.075 ..

TEST-ROOM-EA	= SPACE-CONDITIONS
				ZONE-TYPE		= CONDITIONED
				TEMPERATURE		= (72)
				LIGHTING-SCHEDULE	= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-RV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.356
				LIGHT-RAD-FRAC		= (0.8)
				DAYLIGHTING			= YES
				LIGHT-REF-POINT1		= (60.27,51.45,2.375)
				LIGHT-SET-POINT1		= 60 	
				ZONE-FRACTION1		= 1.0
				LIGHT-CTRL-TYPE1		= CONTINUOUS/OFF
				MIN-LIGHT-FRAC    	= 0.027128791
				MIN-POWER-FRAC		= 0.241853933
				FLOOR-WEIGHT		= 0
				PEOPLE-SCHEDULE		= PEOPLE-SCH
				NUMBER-OF-PEOPLE		= 2 
				PEOPLE-HG-SENS		= 1732.075 ..

TEST-ROOM-EB	= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (72)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-RV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.362
				DAYLIGHTING			= YES
				LIGHT-REF-POINT1		= (60.27,35.75,2.375)
				LIGHT-SET-POINT1		= 60 	
				ZONE-FRACTION1		= 1.0
				LIGHT-CTRL-TYPE1		= CONTINUOUS/OFF
				MIN-LIGHT-FRAC    	= 0.045285457
				MIN-POWER-FRAC		= 0.246480817
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				PEOPLE-SCHEDULE		= PEOPLE-SCH
				NUMBER-OF-PEOPLE		= 2 
				PEOPLE-HG-SENS		= 1732.075 ..


TEST-ROOM-SA	= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (72)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-RV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.364
				DAYLIGHTING			= YES
				LIGHT-REF-POINT1		= (27.05,9.333,2.375)
				LIGHT-SET-POINT1		= 60 	
				ZONE-FRACTION1		= 1.0
				LIGHT-CTRL-TYPE1		= CONTINUOUS/OFF
				MIN-LIGHT-FRAC    	= 0.048764443
				MIN-POWER-FRAC		= 0.242166025
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				PEOPLE-SCHEDULE		= PEOPLE-SCH
				NUMBER-OF-PEOPLE		= 2 
				PEOPLE-HG-SENS		= 1732.075 ..


TEST-ROOM-SB	= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (72)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-RV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.362
				DAYLIGHTING			= YES
				LIGHT-REF-POINT1		= (42.55,9.333,2.375)
				LIGHT-SET-POINT1		= 60
				ZONE-FRACTION1		= 1.0
				LIGHT-CTRL-TYPE1		= CONTINUOUS/OFF
				MIN-POWER-FRAC		= 0.246344828
				MIN-LIGHT-FRAC    	= 0.038429157
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				PEOPLE-SCHEDULE		= PEOPLE-SCH
				NUMBER-OF-PEOPLE		= 2 
				PEOPLE-HG-SENS		= 1732.075 ..




TEST-ROOM-IA		= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (72)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-RV   
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.359
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				PEOPLE-SCHEDULE		= PEOPLE-SCH
				NUMBER-OF-PEOPLE		= 2 
				PEOPLE-HG-SENS		= 1732.075 ..


$ SPACE CONDITION FOR B ROOMS WITH DAYLIGHTING
TEST-ROOM-IB		= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (72)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-RV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.358
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				PEOPLE-SCHEDULE		= PEOPLE-SCH
				NUMBER-OF-PEOPLE		= 2 
				PEOPLE-HG-SENS		= 1732.075 ..




$** SPACE CONDITION FOR INTERIOR ROOM **
INT-SC		= S-C		LIKE TEST-ROOM-A
					EQUIPMENT-KW = 1 ..

$** SPACE CONDITION FOR OTHER ROOMS **
PLENUMS		= S-C		ZONE-TYPE = PLENUM	FLOOR-WEIGHT = 5 ..

$* BREAK ROOM AND STORAGE ROOM *
BREAKROOM-COND	= S-C		LIKE TEST-ROOM-A
					P-SCH = ZERO-SCH
					L-SCH = LIGHT-STANDARD	L-T = REC-FLUOR-RV
					E-SCH = EQP-STANDARD	E-KW = 0.5 ..

$* RECEPTION ROOM, MEDIA CENTER *
MEDIAROOM-COND	= S-C		LIKE TEST-ROOM-A
					P-SCH = PEOPLE-STANDARD	N-O-P = 5
					L-SCH = LIGHT-STANDARD	L-T = REC-FLUOR-RV
					E-SCH = EQP-STANDARD	E-KW = 0.8 ..

$* OFFICE *
OFFICE-COND		= S-C		LIKE TEST-ROOM-A
					P-SCH = PEOPLE-STANDARD	N-O-P = 1
					L-SCH = LIGHT-STANDARD	L-T = REC-FLUOR-RV
					E-SCH = EQP-STANDARD	E-KW = 0.5 ..

$* COMPUTER ROOM AND DISPLAY ROOM *
COMPUTER-COND	= S-C		LIKE TEST-ROOM-A
					P-SCH = PEOPLE-STANDARD	N-O-P = 1
					L-SCH = LIGHT-STANDARD	L-T = REC-FLUOR-RV
					E-SCH = EQP-STANDARD	E-KW = 1 ..

$* CLASS ROOM *
CLASS-COND		= S-C		LIKE TEST-ROOM-A
					P-SCH = PEOPLE-STANDARD	AREA/PERSON = 100
					L-SCH = LIGHT-STANDARD	L-T = REC-FLUOR-RV
					E-SCH = EQP-STANDARD	E-KW = 1 ..

$* MECHANICAL ROOM *
MECHANICAL-COND	= S-C		LIKE TEST-ROOM-A
					PEOPLE-HG-LAT = 205	PEOPLE-HG-SENS = 245
					P-SCH = PEOPLE-STANDARD	N-O-P = 1
					TEMPERATURE = (72.5)
					L-SCH = LIGHT-STANDARD	L-T = SUS-FLUOR
					LIGHTING-W/SQFT = 2.5
					E-SCH = EQP-STANDARD	E-KW = 2 ..	


$*********** SPACE DESCRIPTION OF TEST ROOMS IN ERS ********************

$** DESCRIPTION OF PLENUM IN EAST-A ROOM **
P-EAST-A		= SPACE	
				VOLUME = 1512.5	SPACE-CONDITIONS = PLENUMS ..
	PEWL-EAST-A		= EXTERIOR-WALL
					X = 69.6	Y = 43.5	Z = 8.5
					AZ = 90	TILT = 90
					HEIGHT = 5.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-T ..
	ROOF-EAST-A		= ROOF	
					X = 50.3	Y = 43.5	
					HEIGHT = 15.5	WIDTH = 17.741 ..
	PIW1-EAST-A		= I-W		A = 85.25	N-T = P-MED-1	..
	PIW2-EAST-A		= I-W		A = 94.58	N-T = P-EAST-B 	..
	PIW3-EAST-A		= I-W		A = 94.58	N-T = P-BREAK 	..
	CEIL-EAST-A		= I-W		A = 275	N-T = EASTROOM-A
				      TILT = 180	CONSTRUCTION = CEILING
						INSIDE-VIS-REFL = (0.443,0.443)
						INSIDE-SOL-ABS  = (0.512, 0.512) ..

$** DESCRIPTION OF PLENUM IN SOUTH-A ROOM **
P-SOUTH-A		= SPACE	LIKE P-EAST-A ..
	PEWL-SOUTH-A	= EXTERIOR-WALL
					X = 19.3	Y = 0		Z = 8.5
					AZ = 180	TILT = 90
					HEIGHT = 5.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-T
					GND-REFLECTANCE	=	0.15 ..
	ROOF-SOUTH-A	= ROOF
					X = 19.3	Y = 0
					HEIGHT = 17.741	WIDTH = 15.5 ..
	PIW1-SOUTH-A	= I-W		A = 85.25	N-T = P-MED-1 
							INSIDE-VIS-REFL = (0.836, 0.836)
							INSIDE-SOL-ABS	= (0.212, 0.212) ..
	PIW2-SOUTH-A	= I-W		A = 94.58	N-T = P-SOUTH-B
							INSIDE-VIS-REFL = (0.836, 0.836)
							INSIDE-SOL-ABS	= (0.212, 0.212) ..

	PIW3-SOUTH-A	= I-W		A = 94.58	N-T = P-COMPUTER ..
	CEIL-SOUTH-A	= I-W		A = 275	N-T = SOUTHROOM-A
						TILT = 180	CONSTRUCTION = CEILING
						INSIDE-VIS-REFL = (0.443,0.443)
						INSIDE-SOL-ABS  = (0.512, 0.512) ..



$** DESCRIPTION OF PLENUM IN WEST-A ROOM **
P-WEST-A		= SPACE	LIKE P-EAST-A ..
	PEWL-WEST-A		= EXTERIOR-WALL
					X = 0		Y = 59	Z = 8.5
					AZ = 270	TILT = 90
					HEIGHT = 5.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-T
					GND-REFLECTANCE	=	0.15 ..
	ROOF-WEST-A		= ROOF
					X = 0		Y = 43.5
					HEIGHT = 15.5	WIDTH = 17.741  ..
	PIW1-WEST-A		= I-W		A = 179.83	N-T = P-MED-1 	..
	PIW2-WEST-A		= I-W		A = 94.58	N-T = P-WEST-B 	..
	CEIL-WEST-A		= I-W		A = 275	N-T = WESTROOM-A
						TILT = 180	CONSTRUCTION = CEILING
						INSIDE-VIS-REFL = (0.443,0.443)
						INSIDE-SOL-ABS  = (0.512, 0.512) ..

$** DESCRIPTION OF PLENUM IN INTERIOR-A ROOM **
P-INT-A		= SPACE	LIKE P-EAST-A ..
	ROOF-INT-A		= ROOF
					X = 18.6	Y = 70	
					HEIGHT = 17.741	WIDTH = 15.5 ..
	PIW1-INT-A		= I-W		A = 85.25	N-T = P-MED-1 	..
	PIW2-INT-A		= I-W		A = 94.58	N-T = P-INT-B 	..
	PIW3-INT-A		= I-W		A = 94.58 	N-T = P-DISPLAY ..
	PIW4-INT-A		= I-W		A = 85.25	N-T = MECH-ROOM 	..
	CEIL-INT-A		= I-W		A = 275	N-T = INTROOM-A
						TILT = 180	CONSTRUCTION = CEILING
						INSIDE-VIS-REFL = (0.443,0.443)
						INSIDE-SOL-ABS  = (0.512, 0.512) ..

$** DESCRIPTION OF EAST-A ROOM **
EASTROOM-A		= SPACE
				VOLUME = 2337.5	SPACE-CONDITIONS = TEST-ROOM-EA ..
	REWL-EAST-A		= EXTERIOR-WALL
					X = 69.6	Y = 43.5	Z = 0
					AZ = 90	TILT = 90
					HEIGHT = 8.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-B
					INSIDE-VIS-REFL = 0.836
					INSIDE-SOL-ABS  = 0.112
					GND-REFLECTANCE	=	0.15 ..

EA-Wall	=	R-B	V-T	= REWL-EAST-A	V-L = (1,2,15,16,17,18) ..
	W-1-EAST-A		= WINDOW
				X= 0.158 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH ..

	W-2-EAST-A		= WINDOW
				X= 3.6 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH  ..

	W-3-EAST-A		= WINDOW
				X= 7.04 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH  ..

	W-4-EAST-A		= WINDOW
				X= 10.48 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH  ..

	RIW1-EAST-A		= I-W		AREA = 131.75	NEXT-TO = MEDIA-CENTER	CONS = WALL-INT 
								INSIDE-VIS-REFL = (0.836, 0.836)
								INSIDE-SOL-ABS  = (0.212,0.212) ..
	RIW2-EAST-A		= I-W		AREA = 150.8	NEXT-TO = EASTROOM-B 
								INSIDE-VIS-REFL = (0.836, 0.836)
								INSIDE-SOL-ABS  = (0.212,0.212) ..
	RIW3-EAST-A		= I-W		AREA = 150.8	NEXT-TO = BREAKROOM 
								INSIDE-VIS-REFL = (0.836, 0.836)
								INSIDE-SOL-ABS  = (0.212,0.212) ..
	FLOOR-EAST-A	= UNDERGROUND-FLOOR	
					H = 15.5	W = 17.741
								INSIDE-VIS-REFL =  0.103
								INSIDE-SOL-ABS  =  0.736	 ..

$** DESCRIPTION OF SOUTH-A ROOM **

SOUTHROOM-A		= SPACE
				VOLUME = 2337.5	SPACE-CONDITIONS = TEST-ROOM-SA ..
	REWL-SOUTH-A	= EXTERIOR-WALL
					X = 19.3	Y = 0		Z = 0
					AZ = 180	TILT = 90
					HEIGHT = 8.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-B
					INSIDE-VIS-REFL = 0.836
					INSIDE-SOL-ABS  = 0.112
					GND-REFLECTANCE	=	0.15 ..

SA-Wall	=	R-B	V-T	= REWL-SOUTH-A	V-L = (1,2,15,16,17,18) ..
	W-1-SOUTH-A		= WINDOW
				X= 0.158 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
				OH-W	= 4.27
				OH-D	= 2.0
				OH-B	= 0.67
				OH-A  = 0.825
				R-F-A = 0.67
				R-F-H = 5.67
				R-F-D = 2
				R-F-B = 0.67  ..

	W-2-SOUTH-A		= WINDOW
				X= 3.6 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
 				OH-W	= 3.6
				OH-D	= 2
				OH-B	= 0.67
				OH-A  = 0.158 ..

	W-3-SOUTH-A		= WINDOW
				X= 7.04 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
 				OH-W	= 3.6
				OH-D	= 2
				OH-B	= 0.67
				OH-A  = 0.158 ..

	W-4-SOUTH-A		= WINDOW
				X= 10.48 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
				OH-W	= 4.27
				OH-D	= 2.0
				OH-B	= 0.67
				OH-A  = 0.158
				L-F-A = 0.67
				L-F-H = 5
				L-F-D = 2.0
				L-F-B = -0.67 ..

	RIW1-SOUTH-A	= I-W		AREA = 131.75	NEXT-TO = MEDIA-CENTER 	CONS = WALL-INT
							INSIDE-VIS-REFL = (0.836, 0.836)
							INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW2-SOUTH-A	= I-W		AREA = 150.8	NEXT-TO = SOUTHROOM-B
							INSIDE-VIS-REFL = (0.836, 0.836)
							INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW3-SOUTH-A 	= I-W		AREA = 150.8 	NEXT-TO = COMPUTER-RM
							INSIDE-VIS-REFL = (0.836, 0.836)
							INSIDE-SOL-ABS	= (0.212, 0.212) ..
	FLOOR-SOUTH-A	= UNDERGROUND-FLOOR
					H = 17.741	W = 15.5 INSIDE-VIS-REFL = 0.103
								 INSIDE-SOL-ABS =  0.736 ..

$** DESCRIPTION OF WEST-A ROOM **
WESTROOM-A		= SPACE
				VOLUME = 2337.5	SPACE-CONDITIONS	= TEST-ROOM-WA ..	

REWL-WEST-A		= EXTERIOR-WALL
					X = 0		Y = 59	Z = 0
					AZ = 270	TILT = 90
					HEIGHT = 8.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-B
					INSIDE-VIS-REFL = 0.836
					INSIDE-SOL-ABS  = 0.112
					GND-REFLECTANCE	=	0.15 ..

WA-Wall	=	R-B	V-T	= REWL-WEST-A	V-L = (1,2,15,16,17,18) ..
	W-1-WEST-A		= WINDOW
				X= 0.158 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
					 ..

	W-2-WEST-A		= WINDOW
				X= 3.6 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
 ..

	W-3-WEST-A		= WINDOW
				X= 7.04 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
  ..

	W-4-WEST-A		= WINDOW
				X= 10.48 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH 
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
  ..


	RIW1-WEST-A		= I-W		AREA = 131.75	NEXT-TO = MEDIA-CENTER CONS = WALL-INT
									INSIDE-VIS-REFL = (0.836, 0.836)
									INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW2-WEST-A		= I-W		AREA = 150.8	NEXT-TO = WESTROOM-B 
									INSIDE-VIS-REFL = (0.836, 0.836)
									INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW3-WEST-A 		= I-W		AREA = 150.8 	NEXT-TO = COMPUTER-RM
									INSIDE-VIS-REFL = (0.836, 0.836)
									INSIDE-SOL-ABS	= (0.212, 0.212) ..
	FLOOR-WEST-A		= UNDERGROUND-FLOOR	
					INSIDE-VIS-REFL = 0.103
					INSIDE-SOL-ABS  = 0.736 
					H = 15.5	W = 17.741 	..


$ Irradiance Report
 EAST-WALL-IRRADIANCE	HOURLY-REPORT
		REPORT-SCHEDULE	=	L-REPORT-SCH
		REPORT-BLOCK	=	(EA-Wall)
		OPTION		=	PRINT ..

 SOUTH-WALL-IRRADIANCE	HOURLY-REPORT
		REPORT-SCHEDULE	=	L-REPORT-SCH
		REPORT-BLOCK	=	(SA-Wall)
		OPTION		=	PRINT ..

 WEST-WALL-IRRADIANCE	HOURLY-REPORT
		REPORT-SCHEDULE	=	L-REPORT-SCH
		REPORT-BLOCK	=	(WA-Wall)
		OPTION		=	PRINT ..
$** DESCRIPTION OF INTERIOR-A ROOM **
INTROOM-A		= SPACE
				VOLUME = 2337.5	SPACE-CONDITIONS = TEST-ROOM-IA ..
	RIW1-INT-A		= I-W		AREA = 131.75	NEXT-TO = MEDIA-CENTER	CONS = WALL-INT
								INSIDE-VIS-REFL = (0.836, 0.836)
								INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW2-INT-A		= I-W		AREA = 150.8	NEXT-TO = INTROOM-B
								INSIDE-VIS-REFL = (0.836, 0.836)
								INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW3-INT-A		= I-W		AREA = 150.8	NEXT-TO = DISPLAY-RM
								INSIDE-VIS-REFL = (0.836, 0.836)
								INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW4-INT-A		= I-W		AREA = 131.75	NEXT-TO = MECH-ROOM
								INSIDE-VIS-REFL = (0.836, 0.836)
								INSIDE-SOL-ABS	= (0.212, 0.212) ..
	FLOOR-INT-A		= UNDERGROUND-FLOOR 
					INSIDE-VIS-REFL = 0.103
					INSIDE-SOL-ABS  = 0.736 
					H = 17.741	W = 15.5	U-EFF = 0.005 ..

$** DESCRIPTION OF PLENUM IN EAST-B ROOM **
P-EAST-B		= SPACE	
				VOLUME = 1512.5	SPACE-CONDITIONS = PLENUMS ..
	PEWL-EAST-B		= EXTERIOR-WALL
					X = 69.6	Y = 28	Z = 8.5
					AZ = 90	TILT = 90
					HEIGHT = 5.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-T
					GND-REFLECTANCE	=	0.15 ..
	ROOF-EAST-B		= ROOF	
					X = 50.3	Y = 28	
					HEIGHT = 15.5	WIDTH = 17.741  ..
	PIW1-EAST-B		= I-W		AREA = 85.25	NEXT-TO = P-MED-1 ..
	PIW2-EAST-B		= I-W		AREA = 95.28	NEXT-TO = P-RECEPTION ..
	CEIL-EAST-B		= I-W		AREA = 275		NEXT-TO = EASTROOM-B
						TILT = 180		CONSTRUCTION = CEILING
						INSIDE-VIS-REFL = (0.443,0.443)
						INSIDE-SOL-ABS  = (0.512, 0.512) ..

$** DESCRIPTION OF PLENUM IN SOUTH-B ROOM **
P-SOUTH-B		= SPACE	LIKE P-EAST-B ..
	PEWL-SOUTH-B	= EXTERIOR-WALL
					X = 34.8	Y = 0		Z = 8.5
					AZ = 180	TILT = 90
					HEIGHT = 5.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-T
					INSIDE-VIS-REFL = 0.836
					INSIDE-SOL-ABS  = 0.112
					GND-REFLECTANCE	=	0.15 ..
	ROOF-SOUTH-B	= ROOF
					X = 34.8	Y = 0
					HEIGHT = 17.741	WIDTH = 15.5 ..
	PIW1-SOUTH-B	= I-W		AREA = 85.25	NEXT-TO = P-MED-1 ..
	PIW2-SOUTH-B	= I-W		AREA = 95.28	NEXT-TO = P-OFFICE  ..
	CEIL-SOUTH-B	= I-W		AREA = 275		NEXT-TO = SOUTHROOM-B
						TILT = 180		CONSTRUCTION = CEILING
						INSIDE-VIS-REFL = (0.443,0.443)
						INSIDE-SOL-ABS  = (0.512, 0.512) ..

$** DESCRIPTION OF PLENUM IN WEST-B ROOM **
P-WEST-B		= SPACE	LIKE P-EAST-B ..
	PEWL-WEST-B		= EXTERIOR-WALL
					X = 0		Y = 43.5	Z = 8.5
					AZ = 270	TILT = 90
					HEIGHT = 5.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-T
					GND-REFLECTANCE	=	0.15 ..
	ROOF-WEST-B		= ROOF
					X = 0		Y = 28
					HEIGHT = 15.5	WIDTH = 17.741  ..
	PIW1-WEST-B		= I-W		AREA = 85.25	NEXT-TO = P-MED-1  ..
	PIW2-WEST-B		= I-W		AREA = 95.28	NEXT-TO = P-COMPUTER ..
	CEIL-WEST-B		= I-W		AREA = 275		NEXT-TO = WESTROOM-B
						TILT = 180		CONSTRUCTION = CEILING
						INSIDE-VIS-REFL = (0.443,0.443)
						INSIDE-SOL-ABS  = (0.512, 0.512) ..

$** DESCRIPTION OF PLENUM IN INTERIOR-B ROOM **
P-INT-B		= SPACE	LIKE P-EAST-B ..
	ROOF-INT-B		= ROOF
					X = 34.1	Y = 70	
					HEIGHT = 17.741	WIDTH = 15.5 ..
	PIW1-INT-B		= I-W		AREA = 179.83	NEXT-TO = P-MED-1	..
	PIW2-INT-B		= I-W		AREA = 85.25	NEXT-TO = MECH-ROOM  ..
	CEIL-INT-B		= I-W		AREA = 275		NEXT-TO = INTROOM-B
						TILT = 180		CONSTRUCTION = CEILING
						INSIDE-VIS-REFL = (0.443,0.443)
						INSIDE-SOL-ABS  = (0.512, 0.512) ..

$** DESCRIPTION OF EAST-B ROOM **
EASTROOM-B		= SPACE
				VOLUME = 2337.5	SPACE-CONDITIONS = TEST-ROOM-EB ..
	REWL-EAST-B		= EXTERIOR-WALL
					X = 69.6	Y = 28	Z = 0
					AZ = 90	TILT = 90
					HEIGHT = 8.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-B
					INSIDE-VIS-REFL = 0.836
					INSIDE-SOL-ABS  = 0.112
					GND-REFLECTANCE	=	0.15 ..
	W-1-EAST-B		= WINDOW
				X= 0.158 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH  ..

	W-2-EAST-B		= WINDOW
				X= 3.6 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR 
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH ..

	W-3-EAST-B		= WINDOW
				X= 7.04 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH  ..

	W-4-EAST-B		= WINDOW
				X= 10.48 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH  ..

	RIW1-EAST-B		= I-W		AREA = 131.75	NEXT-TO = MEDIA-CENTER
						CONSTRUCTION = WALL-INT 
						INSIDE-VIS-REFL = (0.836, 0.836)
						INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW2-EAST-B		= I-W		AREA = 150.8	NEXT-TO = RECEPTION-RM
						INSIDE-VIS-REFL = (0.836, 0.836)
						INSIDE-SOL-ABS	= (0.212, 0.212) ..
	FLOOR-EAST-B	= UNDERGROUND-FLOOR
					H = 15.5	W = 17.741
						INSIDE-VIS-REFL = 0.103
						INSIDE-SOL-ABS  = 0.736 	..

$** DESCRIPTION OF SOUTH-B ROOM **
SOUTHROOM-B		= SPACE
				VOLUME = 2337.5	SPACE-CONDITIONS = TEST-ROOM-SB ..
	REWL-SOUTH-B	= EXTERIOR-WALL
					X = 34.8	Y = 0		Z = 0
					AZ = 180	TILT = 90
					HEIGHT = 8.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-B
					INSIDE-VIS-REFL = 0.836
					INSIDE-SOL-ABS  = 0.112
					GND-REFLECTANCE	=	0.15 ..
	W-1-SOUTH-B		= WINDOW
				X= 0.158 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE =  LOW-E2	
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
				OH-W	= 4.27
				OH-D	= 2.0
				OH-B	= 0.67
				OH-A  = 0.825
				R-F-A = 0.67
				R-F-H = 5
				R-F-D = 2.0
				R-F-B = -0.67 ..
			

	W-2-SOUTH-B		= WINDOW
				X= 3.6 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
				OH-W	= 3.6
				OH-D	= 2
				OH-B	= 0.67
				OH-A  = 0.158   ..
				

	W-3-SOUTH-B		= WINDOW
				X= 7.04 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
				OH-W	= 3.6
				OH-D	= 2
				OH-B	= 0.67 ..
				

	W-4-SOUTH-B		= WINDOW
				X= 10.48 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
				VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH				
				OH-W	= 4.27
				OH-D	= 2.0
				OH-B	= 0.67
				OH-A  = 0.158
				L-F-A = 0.67
				L-F-H = 5
				L-F-D = 2.0
				L-F-B = -0.67  ..

	RIW1-SOUTH-B	= I-W		AREA = 131.75	NEXT-TO = MEDIA-CENTER
						CONSTRUCTION = WALL-INT
						INSIDE-VIS-REFL = (0.836, 0.836)
						INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW2-SOUTH-B	= I-W		AREA = 150.8	NEXT-TO = OFFICE
						INSIDE-VIS-REFL = (0.836, 0.836)
						INSIDE-SOL-ABS	= (0.212, 0.212) ..
	FLOOR-SOUTH-B	= UNDERGROUND-FLOOR
					H = 17.741	W = 15.5 
						INSIDE-VIS-REFL = 0.103
						INSIDE-SOL-ABS  = 0.736  ..

$** DESCRIPTION OF WEST-B ROOM **
WESTROOM-B		= SPACE
				VOLUME = 2337.5	SPACE-CONDITIONS = TEST-ROOM-WB ..
	REWL-WEST-B		= EXTERIOR-WALL
					X = 0		Y = 43.5	Z = 0
					AZ = 270	TILT = 90
					HEIGHT = 8.5	WIDTH = 15.5
					CONSTRUCTION = WALL-TESTROOM-B
					INSIDE-VIS-REFL = 0.836
					INSIDE-SOL-ABS  = 0.112
					GND-REFLECTANCE	=	0.15 ..
	W-1-WEST-B		= WINDOW
				X= 0.158 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
				VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
				 ..

	W-2-WEST-B		= WINDOW
				X= 3.6 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
				VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH ..

	W-3-WEST-B		= WINDOW
				X= 7.04 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
				VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH  ..

	W-4-WEST-B		= WINDOW
				X= 10.48 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.158 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
				VIS-TRANS-SCH = TVIS-MUSLIN-SCH 
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH
				SHADING-SCHEDULE = SHADE-SCH-DAYLIGHT
				CONDUCT-SCHEDULE = COND-NYSAN-SCH
				  ..

	RIW1-WEST-B		= I-W		AREA = 131.75	NEXT-TO = MEDIA-CENTER
						CONSTRUCTION = WALL-INT 
						INSIDE-VIS-REFL = (0.836, 0.836)
						INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW2-WEST-B 	= I-W		AREA = 150.8 	NEXT-TO = COMPUTER-RM
							INSIDE-VIS-REFL = (0.836, 0.836)
							INSIDE-SOL-ABS	= (0.212, 0.212) ..
	FLOOR-WEST-B	= UNDERGROUND-FLOOR
					H = 15.5	W = 17.741
								INSIDE-VIS-REFL = 0.103
								INSIDE-SOL-ABS  = 0.736  	 ..

$** DESCRIPTION OF INTERIOR-B ROOM **
INTROOM-B		= SPACE
				VOLUME = 2337.5	SPACE-CONDITIONS = TEST-ROOM-IB ..
	RIW1-INT-B		= I-W		AREA = 282.55	NEXT-TO = MEDIA-CENTER
						CONSTRUCTION = WALL-INT 
								INSIDE-VIS-REFL = (0.836, 0.836)
								INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW2-INT-B		= I-W		AREA = 131.75	NEXT-TO = MECH-ROOM 
								INSIDE-VIS-REFL = (0.836, 0.836)
								INSIDE-SOL-ABS	= (0.212, 0.212) ..
	FLOOR-INT-B		= UNDERGROUND-FLOOR 
					H = 17.741	W = 15.5	U-EFF = 0.005
								INSIDE-VIS-REFL = 0.103
								INSIDE-SOL-ABS  = 0.736  ..

$*********** SPACE DESCRIPTION OF OTHER ROOMS IN ERS ********************

$** DESCRIPTION OF PLENUM IN BREAK ROOM **
P-BREAK		= SPACE	
				V = 2341.8	A = 390.3	SPACE-CONDITIONS = PLENUMS ..
	PEWL-BREAK		= EXTERIOR-WALL
					X = 69.6	Y = 59	Z = 8
					AZ = 90	TILT = 90
					HEIGHT = 6	WIDTH = 36.6
					CONSTRUCTION = WALL-TOP ..
	ROOF-BREAK		= ROOF	
					X = 58.94	Y = 59	
					HEIGHT = 36.6	WIDTH = 10.66  ..
	PIW1-BREAK		= I-W		AREA = 63.96	NEXT-TO = MECH-ROOM 	 ..
	PIW2-BREAK		= I-W		AREA = 219.6	NEXT-TO = P-MED-1 	 ..
	CEIL-BREAK		= I-W		AREA = 390.3	NEXT-TO = BREAKROOM
						TILT = 180		CONSTRUCTION = CEILING ..

$** DESCRIPTION OF PLENUM IN RECEPTION AREA **
P-RECEPTION 	= SPACE	
				V = 1268.48	A = 230.63	SPACE-CONDITIONS = PLENUMS ..
	PEWL-RECEPTION	= EXTERIOR-WALL
					X = 66.6	Y = 15	Z = 8.5
					AZ = 90	TILT = 90 
					HEIGHT = 5.5	WIDTH = 13
					CONSTRUCTION = WALL-OVERHEAD ..
	ROOF-RECEPTION 	= ROOF	
					X = 50.3	Y = 15
					HEIGHT = 13		WIDTH = 17.741 ..
	CEIL-RECEPTION	= I-W		AREA = 230.63	NEXT-TO = RECEPTION-RM
						TILT = 180		CONSTRUCTION = CEILING ..

$** DESCRIPTION OF PLENUM IN OFFICE **
P-OFFICE 		= SPACE
				V = 1087.8	A = 197.8	SPACE-CONDITIONS = PLENUMS ..
	PEW1-OFFICE		= EXTERIOR-WALL
					X = 66.6	Y = 3		Z = 8.5
					AZ = 90	TILT = 90
					HEIGHT = 5.5	WIDTH = 12.1
					CONSTRUCTION = WALL-OVERHEAD ..
	PEW2-OFFICE		= EXTERIOR-WALL
					X = 34.2	Y = 0		Z = 8.5
					AZ = 180	TILT = 90
					HEIGHT = 5.5	WIDTH = 16.4
					CONSTRUCTION = WALL-OVERHEAD ..
	ROOF-OFFICE 	= ROOF 
					X = 50.3	Y = 3
					HEIGHT = 12.1	WIDTH = 16.4 ..
	CEIL-OFFICE 	= I-W		AREA = 197.8	NEXT-TO = OFFICE 
						TILT = 180		CONSTRUCTION = CEILING ..

$** DESCRIPTION OF PLENUM IN COMPUTER ROOM **
P-COMPUTER 		= SPACE
				V = 2284.3	A = 415.3	SPACE-CONDITIONS = PLENUMS ..
	PEW1-CMPTR		= EXTERIOR-WALL
					X = 3		Y = 3		Z = 8.5
					AZ = 180	TILT = 90
					HEIGHT = 5.5	WIDTH = 16.3
					CONSTRUCTION = WALL-OVERHEAD ..
	PEW2-CMPTR		= EXTERIOR-WALL
					X = 3		Y = 28	Z = 8.5
					AZ = 270	TILT = 90
					HEIGHT = 5.5	WIDTH = 25.1
					CONSTRUCTION = WALL-OVERHEAD ..
	ROOF-CMPTR	 	= ROOF 
					X = 3		Y = 3
					HEIGHT = 25.1	WIDTH = 16.3  ..
	CEIL-CMPTR	 	= I-W		AREA = 415.3	NEXT-TO = COMPUTER-RM 
						TILT = 180		CONSTRUCTION = CEILING ..

$** DESCRIPTION OF PLENUM IN WEST CLASS ROOM **
P-CLASS-W		= SPACE
				V = 769.7	A = 769.7	SPACE-CONDITIONS = PLENUMS ..
	PEW1-CLASS-W	= EXTERIOR-WALL
					X = -22.2	Y = 65	Z = 9
					AZ = 180	TILT = 90
					HEIGHT = 1	WIDTH = 22.2
					CONSTRUCTION = WALL-CLASSROOM ..
	PEW2-CLASS-W	= EXTERIOR-WALL
					X = -22.2	Y = 99.3	Z = 9
					AZ = 270	TILT = 90
					HEIGHT = 1	WIDTH = 34.67
					CONSTRUCTION = WALL-CLASSROOM ..
	PEW3-CLASS-W	= EXTERIOR-WALL
					X = 0		Y = 99.3	Z = 9
					AZ = 0	TILT = 90
					HEIGHT = 1	WIDTH = 22.2
					CONSTRUCTION = WALL-CLASSROOM ..
	ROOF-CLASS-W 	= ROOF 
					X = -22.5		Y = 65
					HEIGHT = 34.67	WIDTH = 22.2
					CONSTRUCTION = ROOF-CLASS ..
	CEIL-CLASS-W 	= I-W		AREA = 796.7	NEXT-TO = CLASSROOM-W
						TILT = 180		CONSTRUCTION = CEILING ..

$** DESCRIPTION OF PLENUM IN EAST CLASS ROOM **
P-CLASS-E		= SPACE
				V = 769.7	A = 769.7	SPACE-CONDITIONS = PLENUMS ..
	PEW1-CLASS-E	= EXTERIOR-WALL
					X = 91.8	Y = 65	Z = 9
					AZ = 180	TILT = 90
					HEIGHT = 1	WIDTH = 22.2
					CONSTRUCTION = WALL-CLASSROOM ..
	PEW2-CLASS-E	= EXTERIOR-WALL
					X = 91.8	Y = 99.3	Z = 9
					AZ = 90	TILT = 90
					HEIGHT = 1	WIDTH = 34.67
					CONSTRUCTION = WALL-CLASSROOM ..
	PEW3-CLASS-E	= EXTERIOR-WALL
					X = 69.6	Y = 99.3	Z = 9
					AZ = 0	TILT = 90
					HEIGHT = 1	WIDTH = 22.2
					CONSTRUCTION = WALL-CLASSROOM ..
	ROOF-CLASS-E 	= ROOF 
					X = 91.8		Y = 65
					HEIGHT = 34.67	WIDTH = 22.2 
					CONSTRUCTION = ROOF-CLASS ..
	CEIL-CLASS-E 	= I-W		AREA = 796.7	NEXT-TO = CLASSROOM-E
						TILT = 180		CONSTRUCTION = CEILING ..

$** DESCRIPTION OF PLENUM IN DISPLAY ROOM **
P-DISPLAY		= SPACE
				V = 1740.4	A = 316.4	SPACE-CONDITIONS = PLENUMS ..
	PEW1-DISPLAY	= EXTERIOR-WALL
					X = 0		Y = 88	Z = 10
					AZ = 270	TILT = 90
					HEIGHT = 4	WIDTH = 17.741
					CONSTRUCTION = WALL-TOP ..
	ROOF-DISPLAY	= ROOF 
					X = 0		Y = 70
					HEIGHT = 17.741	WIDTH = 17.783 ..
	PIWL-DISPLAY	= I-W		AREA = 98.07	NEXT-TO = MECH-ROOM  ..
	CEIL-DISPLAY	= I-W		AREA = 316.4	NEXT-TO = DISPLAY-RM
						TILT = 180		CONSTRUCTION = CEILING ..

$** DESCRIPTION OF PLENUM IN MEDIA CENTER **
P-MED-1		= SPACE
				V = 7751.6	A = 1824.1	SPACE-CONDITIONS = PLENUMS ..
	PEW1-MED-1		= EXTERIOR-WALL
					X = 0			Y = 65	Z = 8.5
					AZ = 270		TILT = 90
					HEIGHT = 5.5	WIDTH = 6
					CONSTRUCTION = WALL-TOP ..
	ROOF-MED-1		= ROOF 
					X = 17.75		Y = 17.75
					HEIGHT = 60.8	WIDTH = 30 ..
	PIW1-MED-1		= I-W		AREA = 33		NEXT-TO = MECH-ROOM ..
	CEIL-MED-1		= I-W		AREA = 1824.1	NEXT-TO = MEDIA-CENTER
						TILT = 180		CONSTRUCTION = CEILING ..

$** DESCRIPTION OF BREAK ROOM **
BREAKROOM		= SPACE
				V = 3122.4	A = 390.3	SPACE-CONDITIONS = BREAKROOM-COND ..
	REWL-BREAK		= EXTERIOR-WALL
					X = 69.6	Y = 59
					AZ = 90	TILT = 90
					HEIGHT = 8	WIDTH = 36.6
					CONSTRUCTION = WALL-BOTTOM ..
	RIW1-BREAK		= I-W		AREA = 85.28	NEXT-TO = STORAGE-RM 	..
	RIW2-BREAK		= I-W		AREA = 292.8	NEXT-TO = MEDIA-CENTER 	..
	FLOOR-BREAK		= U-F		HEIGHT = 36.6	WIDTH = 10.66 	 ..

$** DESCRIPTION OF RECEPTION ROOM **
RECEPTION-RM 	= SPACE
				V = 1960.36	A = 230.63	SPACE-CONDITIONS = MEDIAROOM-COND ..
	REWL-RECEPT		= EXTERIOR-WALL
					X = 66.6		Y = 15
					AZ = 90		TILT = 90
					HEIGHT = 8.5	WIDTH = 13
					CONSTRUCTION = WALL-SPANDRELL ..
	WIND-RECEPT		= WINDOW	G-T = WINDOW-TYPICAL	H = 5	W = 7.9 ..
	RIW1-RECEPT		= I-W		AREA = 150.8	NEXT-TO = OFFICE 	 ..
	FLOOR-RECEPT	= U-F		HEIGHT = 13		WIDTH = 17.741 	 ..

$** DESCRIPTION OF OFFICE **
OFFICE 		= SPACE
				V = 1681.2	A = 197.8	SPACE-CONDITIONS = OFFICE-COND ..
	REW1-OFFICE		= EXTERIOR-WALL
					X = 66.6		Y = 3
					AZ = 90		TILT = 90
					HEIGHT = 8.5	WIDTH = 12.1
					CONSTRUCTION = WALL-SPANDRELL ..
	WIN1-OFFICE		= WINDOW	G-T = WINDOW-TYPICAL	H = 5	W = 11.8 ..
	REW2-OFFICE		= EXTERIOR-WALL
					X = 50.3		Y = 3
					AZ = 180		TILT = 90
					HEIGHT = 8.5	WIDTH = 16.4
					CONSTRUCTION = WALL-SPANDRELL ..
	WIN2-OFFICE		= WINDOW	G-T = WINDOW-TYPICAL	H = 5	W = 15.3 ..
	FLOOR-OFFICE	= U-F		HEIGHT = 12.1		WIDTH = 16.4
						CONS = GND-FLOOR ..

$** DESCRIPTION OF COMPUTER ROOM **
COMPUTER-RM 	= SPACE
				V = 3530.3	A = 415.3	SPACE-CONDITIONS = COMPUTER-COND ..
	REW1-COMP		= EXTERIOR-WALL
					X = 3			Y = 3
					AZ = 180		TILT = 90
					HEIGHT = 8.5	WIDTH = 16.3
					CONSTRUCTION = WALL-SPANDRELL ..
	WIN1-COMP		= WINDOW	G-T = WINDOW-TYPICAL	H = 5	W = 15.3 ..
	REW2-COMP		= EXTERIOR-WALL
					X = 3			Y = 28
					AZ = 270		TILT = 90
					HEIGHT = 8.5	WIDTH = 25.1
					CONSTRUCTION = WALL-SPANDRELL ..
	WIN2-COMP		= WINDOW	G-T = WINDOW-TYPICAL	H = 5	W = 24 ..
	RIW1-COMP		= I-W		A = 85	NEXT-TO = DISPLAY-RM 	 ..
	FLOOR-COMP		= U-F		HEIGHT = 25.1	WIDTH = 16.3 	 ..

$** DESCRIPTION OF WEST CLASSROOM **
CLASSROOM-W		= SPACE	
				V = 3530.3	A = 415.3	SPACE-CONDITIONS = CLASS-COND ..
	REW1-CLASS-W	= EXTERIOR-WALL
					X = -22.2		Y = 65
					AZ = 180		TILT = 90
					HEIGHT = 9		WIDTH = 22.2
					CONSTRUCTION = WALL-CLASSROOM ..
	WIN1-CLASS-W	= WINDOW	G-T = WINDOW-TYPICAL	H = 5	W = 3.5 ..
	REW2-CLASS-W	= EXTERIOR-WALL
					X = -22.2		Y = 99.3
					AZ = 270		TILT = 90
					HEIGHT = 9		WIDTH = 34.67
					CONSTRUCTION = WALL-CLASSROOM ..
	WIN2-CLASS-W	= WINDOW	G-T = WINDOW-TYPICAL	H = 5	W = 7 ..
	REW3-CLASS-W	= EXTERIOR-WALL
					X = 0			Y = 99.3
					AZ = 0		TILT = 90
					HEIGHT = 9		WIDTH = 22.2
					CONSTRUCTION = WALL-CLASSROOM ..
	WIN3-CLASS-W	= WINDOW	G-T = WINDOW-TYPICAL	H = 5	W = 3.5 ..
	RIW1-CLASS-W	= I-W		A = 85	NEXT-TO = DISPLAY-RM 	 ..
	FLOOR-CLASS-W	= U-F		HEIGHT = 34.67	WIDTH = 22.2 	 ..

$** DESCRIPTION OF EAST CLASSROOM **
CLASSROOM-E		= SPACE	
				V = 3530.3	A = 415.3	SPACE-CONDITIONS = CLASS-COND ..
	REW1-CLASS-E	= EXTERIOR-WALL
					X = 91.8		Y = 65
					AZ = 180		TILT = 90
					HEIGHT = 9		WIDTH = 22.2
					CONSTRUCTION = WALL-CLASSROOM ..
	WIN1-CLASS-E	= WINDOW	G-T = WINDOW-TYPICAL	H = 5	W = 3.5 ..
	REW2-CLASS-E	= EXTERIOR-WALL
					X = 91.8		Y = 99.3
					AZ = 90		TILT = 90
					HEIGHT = 9		WIDTH = 34.67
					CONSTRUCTION = WALL-CLASSROOM ..
	WIN2-CLASS-E	= WINDOW	G-T = WINDOW-TYPICAL	H = 5	W = 7 ..
	REW3-CLASS-E	= EXTERIOR-WALL
					X = 69.6		Y = 99.3
					AZ = 0		TILT = 90
					HEIGHT = 9		WIDTH = 22.2
					CONSTRUCTION = WALL-CLASSROOM ..
	WIN3-CLASS-E	= WINDOW	G-T = WINDOW-TYPICAL	H = 5	W = 3.5 ..
	RIW1-CLASS-E	= I-W		A = 85	NEXT-TO = BREAKROOM 	..
	FLOOR-CLASS-E	= U-F		HEIGHT = 34.67	WIDTH = 22.2 	..

$** DESCRIPTION OF DISPLAY ROOM **
DISPLAY-RM 		= SPACE
				V = 2689.7	A = 316.4	SPACE-CONDITIONS = COMPUTER-COND ..
	RIW1-DISP		= I-W		A = 151.56	NEXT-TO = MECH-ROOM ..
	RIW2-DISP		= I-W		A = 150.80	NEXT-TO = P-MED-1 ..
	FLOOR-DISP		= U-F		H = 17.741	W = 17.83 ..

$** DESCRIPTION OF STORAGE ROOM **
STORAGE-RM		= SPACE
				V = 2689.7	A = 316.4	SPACE-CONDITIONS = BREAKROOM-COND ..
	REW1-STORE		= EXTERIOR-WALL
					X = 69.6		Y = 95.6
					AZ = 90		TILT = 90
					HEIGHT = 8.5	WIDTH = 25.3
					CONSTRUCTION = WALL-BOTTOM ..
	REW2-STORE		= EXTERIOR-WALL
					X = 69.6		Y = 118.6
					AZ = 0		TILT = 90
					HEIGHT = 8.5	WIDTH = 10.52
					CONSTRUCTION = WALL-BOTTOM ..
	RIW1-STORE		= I-W		A = 215.05	NEXT-TO = MECH-ROOM 	 ..
	RIW2-STORE		= I-W		A = 266.1	NEXT-TO = MECH-ROOM 	TILT = 0 ..
	FLOOR-STORE		= U-F		HEIGHT = 25.3	WIDTH = 10.55  ..

$** DESCRIPTION OF MEDIA CENTER **
MEDIA-CENTER	= SPACE
				V = 19187.4	A = 1924.1	SPACE-CONDITIONS = MEDIAROOM-COND ..
	REWL-MEDIA		= EXTERIOR-WALL
					X = 0			Y = 65
					AZ = 270		TILT = 90
					HEIGHT = 8.5	WIDTH = 6 
					CONSTRUCTION = WALL-BOTTOM ..
	ROOF-MEDIA		= ROOF	X = 29.8	Y = 38.5	H = 10.5	W = 10.5 ..
	WIND-MEDIA		= WINDOW
					X = 0		Y = 0	
					H = 10	W = 10.5
					G-T = WINDOW-SKYLITE ..	
	RIW1-MEDIA		= I-W		A = 51	NEXT-TO = MECH-ROOM ..
	FLOOR-MEDIA		= U-F		HEIGHT = 64.14	WIDTH = 30 ..

$** DESCRIPTION OF MECHANICAL ROOM **
MECH-ROOM		= SPACE
				V = 26159	A = 1764	SPACE-CONDITIONS = MECHANICAL-COND ..
	REW1-MECH		= EXTERIOR-WALL
					X = 0			Y = 118.6
					AZ = 270		TILT = 90
					HEIGHT = 14		WIDTH = 19.1
					CONSTRUCTION = WALL-TOP ..
	REW2-MECH		= EXTERIOR-WALL
					X = 59.1		Y = 118.6
					AZ = 0		TILT = 90
					HEIGHT = 14		WIDTH = 57.8
					CONSTRUCTION = WALL-TOP ..
	REW3-MECH		= EXTERIOR-WALL
					X = 69.6		Y = 95.6	Z = 8.5
					AZ = 90		TILT = 90
					HEIGHT = 5.5	WIDTH = 25.3
					CONSTRUCTION = WALL-TOP ..
	REW4-MECH		= EXTERIOR-WALL
					X = 0			Y = 99.3	Z = 10
					AZ = 270		TILT = 90
					HEIGHT = 4		WIDTH = 11.3
					CONSTRUCTION = WALL-TOP ..
	ROOF-MECH		= ROOF	X = 0	Y = 88	H = 30.6	W = 66.3 ..
	FLOOR-MECH		= U-F		HEIGHT = 30.6 WIDTH = 57.5 ..	

$****************** REPORTS ******************************
$** VERIFICATION AND SUMMARY REPORT **
$LOADS-REPORT	VERIFICATION 	= (LV-D)	
$			SUMMARY	 	= (LS-C)
$			REPORT-FREQUENCY 	= HOURLY
$			HOURLY-DATA-SAVE 	= FORMATTED ..

$ LV-D = DETAILS OF EXTERIOR SURFACE IN THE PROJECT
$ LS-C = BUILDING PEAK LOAD COMPONENTS

$** LOAD HOURLY REPORT **
L-REPORT-SCH	= SCHEDULE THRU DEC 31 (ALL) (1,24) (1) ..

RS	= R-B V-T = GLOBAL	V-L = (4,3,13,14,15) ..

$* REPORT BLOCK FOR SPACE ELECTRIC FROM LIGHT WITH VARIABLE LIST 45
RL-EALO	= R-B	V-T = EASTROOM-A	V-L = (44, 25, 12) ..
RL-EBLO	= R-B	V-T = EASTROOM-B	V-L = (44, 25, 12) ..
RL-IALO	= R-B	V-T = INTROOM-A	V-L = (44, 25, 12) ..
RL-IBLO	= R-B	V-T = INTROOM-B	V-L = (44, 25, 12) ..
RL-SALO	= R-B	V-T = SOUTHROOM-A	V-L = (44, 25, 12) ..
RL-SBLO	= R-B	V-T = SOUTHROOM-B	V-L = (44, 25, 12) ..
RL-WALO	= R-B	V-T = WESTROOM-A	V-L = (44, 25, 12) ..
RL-WBLO	= R-B	V-T = WESTROOM-B	V-L = (44, 25, 12) ..




HOURLY-LOAD0	= HOURLY-REPORT
			REPORT-SCHEDULE	= L-REPORT-SCH
			REPORT-BLOCK	= (RL-EALO,RL-EBLO,RL-IALO,RL-IBLO,
						   RL-SALO,RL-SBLO,RL-WALO,RL-WBLO)
			OPTION		= PRINT ..

$* REPORT BLOCK FOR SPACE ELECTRIC FROM LIGHT WITH VARIABLE LIST 45
RL-EAL	= R-B	V-T = EASTROOM-A	V-L = (45) ..
RL-EBL	= R-B	V-T = EASTROOM-B	V-L = (45) ..
RL-IAL	= R-B	V-T = INTROOM-A	V-L = (45) ..
RL-IBL	= R-B	V-T = INTROOM-B	V-L = (45) ..
RL-SAL	= R-B	V-T = SOUTHROOM-A	V-L = (45) ..
RL-SBL	= R-B	V-T = SOUTHROOM-B	V-L = (45) ..
RL-WAL	= R-B	V-T = WESTROOM-A	V-L = (45) ..
RL-WBL	= R-B	V-T = WESTROOM-B	V-L = (45) ..




HOURLY-LOAD1	= HOURLY-REPORT
			REPORT-SCHEDULE	= L-REPORT-SCH
			REPORT-BLOCK	= (RL-EAL,RL-EBL,RL-IAL,RL-IBL,
						   RL-SAL,RL-SBL,RL-WAL,RL-WBL)
			OPTION		= PRINT ..

RL-EALX	= R-B	V-T = EASTROOM-A	V-L = (49) ..
RL-EBLX	= R-B	V-T = EASTROOM-B	V-L = (49) ..
RL-IALX	= R-B	V-T = INTROOM-A	V-L = (49) ..
RL-IBLX	= R-B	V-T = INTROOM-B	V-L = (49) ..
RL-SALX	= R-B	V-T = SOUTHROOM-A	V-L = (49) ..
RL-SBLX	= R-B	V-T = SOUTHROOM-B	V-L = (49) ..
RL-WALX	= R-B	V-T = WESTROOM-A	V-L = (49) ..
RL-WBLX	= R-B	V-T = WESTROOM-B	V-L = (49) ..

HOURLY-LOAD2	= HOURLY-REPORT
			REPORT-SCHEDULE	= L-REPORT-SCH
			REPORT-BLOCK	= (RL-EALX,RL-EBLX,RL-IALX,RL-IBLX,
						   RL-SALX,RL-SBLX,RL-WALX,RL-WBLX)
			OPTION		= PRINT ..

WEATHER-LOAD	= HOURLY-REPORT
			REPORT-SCHEDULE	= L-REPORT-SCH
			REPORT-BLOCK	= (RS)
			OPTION		= PRINT ..

WINDOW-OUT1		=	R-B	V-T	= W-1-EAST-A   V-L	= (13,22) ..
WINDOW-OUT2		=	R-B	V-T	= W-2-EAST-A   V-L	= (13,22) ..
WINDOW-OUT3		=	R-B	V-T	= W-3-EAST-A   V-L	= (13,22) ..
WINDOW-OUT4		=	R-B	V-T	= W-4-EAST-A   V-L	= (13,22) .. 

HOURLY-LOAD3	= HOURLY-REPORT
			REPORT-SCHEDULE	= L-REPORT-SCH
			REPORT-BLOCK	= (WINDOW-OUT1,WINDOW-OUT2,WINDOW-OUT3,WINDOW-OUT4)
			OPTION		= PRINT ..
END ..
COMPUTE LOADS ..


$*********************************************************************************
$                    	INPUT FOR ERS HVAC SYSTEM                                *
$*********************************************************************************
INPUT SYSTEMS	INPUT-UNITS = METRIC	OUTPUT-UNITS = METRIC ..


$****************** SCHEDULE FOR ZONE TEMPERATURES *****************************
$** HEATING SET POINT **
HEAT-SPT	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) TEMP = (22) ..

$** COOLING SET POINT **
COOL-SPT	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) TEMP = (22) ..

$***************** SCHEDULE FOR SUPPLY FAN **************************************
FAN-SCH	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) VALUES = (1) ..

$**************** SCHEDULE FOR OUTSIDE AIR **************************************
OA-SCH-A 	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) VALUES = (0) ..

OA-SCH-B	=SCHEDULE THRU DEC 31
			(ALL) (1,24) VALUES = (0)  ..

$**************** SCHEDULE FOR SYSTEM CONTROL ***********************************
$** HEATING SCHEDULE **
HEAT-SCH	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) VALUES = (1)  ..

$** COOLING SCHEDULE **
COOL-SCH	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) VALUES = (1)  ..

$********************* ZONE CONTROL **********************************************
ZONE-CTRL	= ZONE-CONTROL
			DESIGN-HEAT-T	= 22
			HEAT-TEMP-SCH	= HEAT-SPT
			DESIGN-COOL-T	= 23
			COOL-TEMP-SCH	= COOL-SPT
			THERMOSTAT-TYPE	= PROPORTIONAL
			THROTTLING-RANGE	= 0.1 ..

$********************* ZONE AIR **************************************************
ZA-TEST		= ZONE-AIR		ASSIGNED-CFM	= 1000 ..
ZA-INT		= ZONE-AIR		ASSIGNED-CFM	= 700 ..
ZA-BREAK		= ZONE-AIR		ASSIGNED-CFM	= 500 ..
ZA-RECEPT		= ZONE-AIR		ASSIGNED-CFM	= 600 ..
ZA-OFFICE		= ZONE-AIR		ASSIGNED-CFM	= 600 ..
ZA-CMPTR		= ZONE-AIR		ASSIGNED-CFM	= 2000 ..
ZA-CLASS		= ZONE-AIR		ASSIGNED-CFM	= 2000 ..
ZA-DISPLAY		= ZONE-AIR		ASSIGNED-CFM	= 2000 ..
ZA-STOR		= ZONE-AIR		ASSIGNED-CFM	= 300 ..
ZA-MEDIA		= ZONE-AIR		ASSIGNED-CFM	= 2500 ..
ZA-MECH		= ZONE-AIR		ASSIGNED-CFM	= 2500 ..


$*********************** ZONES OPERATION ******************************************
$** TEST ROOMS A **
P-EAST-A	= ZONE	ZONE-TYPE	= PLENUM ..
P-SOUTH-A	= ZONE	ZONE-TYPE	= PLENUM ..
P-WEST-A	= ZONE	ZONE-TYPE	= PLENUM ..
P-INT-A		= ZONE	ZONE-TYPE	= PLENUM ..

EASTROOM-A	= ZONE
		ZONE-TYPE		= CONDITIONED
		ZONE-CONTROL	= ZONE-CTRL
		ZONE-AIR		= ZA-TEST
		M-C-R			= 0.8
		TERMINAL-TYPE	= SVAV ..

SOUTHROOM-A	= ZONE 	LIKE EASTROOM-A ..
WESTROOM-A	= ZONE	LIKE EASTROOM-A ..
INTROOM-A	= ZONE	LIKE EASTROOM-A	Z-A = ZA-INT	M-C-R = 0.606796 ..

$** TEST ROOMS B **
P-EAST-B	= ZONE	ZONE-TYPE	= PLENUM ..
P-SOUTH-B	= ZONE	ZONE-TYPE	= PLENUM ..
P-WEST-B	= ZONE	ZONE-TYPE	= PLENUM ..
P-INT-B	= ZONE	ZONE-TYPE	= PLENUM ..

EASTROOM-B	= ZONE	LIKE EASTROOM-A ..
SOUTHROOM-B	= ZONE 	LIKE EASTROOM-A ..
WESTROOM-B	= ZONE	LIKE EASTROOM-A ..
INTROOM-B	= ZONE	LIKE INTROOM-A ..

$** OTHER ROOMS IN ERS **
P-BREAK	= ZONE	ZONE-TYPE	= PLENUM ..
P-RECEPTION	= ZONE	ZONE-TYPE	= PLENUM ..
P-OFFICE	= ZONE	ZONE-TYPE	= PLENUM ..
P-COMPUTER	= ZONE	ZONE-TYPE	= PLENUM ..
P-CLASS-W	= ZONE	ZONE-TYPE	= PLENUM ..
P-CLASS-E	= ZONE	ZONE-TYPE	= PLENUM ..
P-DISPLAY	= ZONE	ZONE-TYPE	= PLENUM ..
P-MED-1	= ZONE	ZONE-TYPE	= PLENUM ..

BREAKROOM		= ZONE	LIKE EASTROOM-A	Z-A = ZA-BREAK	M-C-R = 0.308 ..
RECEPTION-RM	= ZONE	LIKE EASTROOM-A	Z-A = ZA-RECEPT	M-C-R = 0.113 ..
OFFICE		= ZONE	LIKE EASTROOM-A	Z-A = ZA-OFFICE	M-C-R = 0.063 ..
COMPUTER-RM		= ZONE	LIKE EASTROOM-A	Z-A = ZA-CMPTR	M-C-R = 0.08 ..
CLASSROOM-W		= ZONE 	LIKE EASTROOM-A	Z-A = ZA-CLASS	M-C-R = 0.313 ..
CLASSROOM-E		= ZONE 	LIKE EASTROOM-A	Z-A = ZA-CLASS	M-C-R = 0.313 ..
DISPLAY-RM		= ZONE 	LIKE EASTROOM-A	Z-A = ZA-DISPLAY	M-C-R = 0.25 ..
STORAGE-RM		= ZONE 	LIKE EASTROOM-A	Z-A = ZA-STOR	M-C-R = 0.0 ..
MEDIA-CENTER	= ZONE 	LIKE EASTROOM-A	Z-A = ZA-MEDIA	M-C-R = 0.14 ..
MECH-ROOM		= ZONE 	LIKE EASTROOM-A	Z-A = ZA-MECH	M-C-R = 0.29 ..


$********************* SYSTEM CONTROL ********************************************
$** TEST ROOMS SYSTEMS **
SC-TEST	= SYSTEM-CONTROL
			MAX-SUPPLY-T		= 50
			MIN-SUPPLY-T		= 14.7
			HEATING-SCHEDULE		= HEAT-SCH
			COOLING-SCHEDULE		= COOL-SCH 
			COOL-CONTROL		= CONSTANT
			COOL-SET-T			= 14.2 ..
			

SC-MAIN	= SYSTEM-CONTROL
			MAX-SUPPLY-T		= 35
			MIN-SUPPLY-T		= 13
			HEATING-SCHEDULE		= HEAT-SCH
			COOLING-SCHEDULE		= COOL-SCH
			COOL-CONTROL		= CONSTANT
			COOL-SET-T			= 13 ..

$********************* SYSTEM AIR ***********************************************
SA-TEST	= SYSTEM-AIR
			OA-CONTROL			= FIXED
			DUCT-AIR-LOSS		= 0
			MIN-OUTSIDE-AIR		= 0
			DUCT-DELTA-T		= 0  ..
SB-TEST	= SYSTEM-AIR
			OA-CONTROL			= FIXED
			DUCT-AIR-LOSS		= 0
			MIN-OUTSIDE-AIR		= 0
			DUCT-DELTA-T		= 0 ..
SA-MAIN	= SYSTEM-AIR
			OA-CONTROL			= TEMP
			SUPPLY-CFM			= 6000
			MIN-OUTSIDE-AIR		= 0.07
			DUCT-AIR-LOSS		= 0
			DUCT-DELTA-T 		= 0.5 ..

$******************** SYSTEM FAN ****************************************************
SYSTEM-FAN-ALL	= SYSTEM-FANS
			FAN-SCHEDULE		=  FAN-SCH
			FAN-CONTROL 		=  INLET
			SUPPLY-DELTA-T		=  0.0000001
			SUPPLY-KW			=  0.0000001 ..	
			$SUPPLY-STATIC		=  25.4 ..
			$SUPPLY-EFF			=  0.7 ..


$****************** SYSTEM TERMINAL ************************************************
ST-TEST	= SYSTEM-TERMINAL		REHEAT-DELTA-T = 40 	 ..
ST-MAIN	= SYSTEM-TERMINAL		REHEAT-DELTA-T = 40	MIN-CFM-RATIO = 0.07 ..


$******************** SYSTEMS EQUIPMENT ********************************************
SE-TEST = SYSTEM-EQUIPMENT
			C-CAP = 10000000 ..
$******************** SYSTEMS OPERATION ********************************************
AHU-A		= SYSTEM
			SYSTEM-TYPE			= VAVS
			PLENUM-NAMES		= (P-EAST-A,P-SOUTH-A,P-WEST-A)
			ZONE-NAMES			= (P-EAST-A,P-SOUTH-A,P-WEST-A,P-INT-A,
						   		EASTROOM-A,SOUTHROOM-A,WESTROOM-A,INTROOM-A) 
			ZONE-HEAT-SOURCE 		= ELECTRIC
			RETURN-AIR-PATH		= PLENUM-ZONES
			SYSTEM-CONTROL		= SC-TEST
			SYSTEM-AIR			= SA-TEST
			SYSTEM-EQUIPMENT		= SE-TEST
			SYSTEM-FANS			= SYSTEM-FAN-ALL
			SYSTEM-TERMINAL		= ST-TEST ..

AHU-B		= SYSTEM
			SYSTEM-CONTROL		= SC-TEST
			SYSTEM-AIR			= SB-TEST
			SYSTEM-EQUIPMENT		= SE-TEST
			SYSTEM-FANS			= SYSTEM-FAN-ALL
			SYSTEM-TERMINAL		= ST-TEST
			SYSTEM-TYPE			= VAVS
			PLENUM-NAMES		= 	(P-EAST-B,P-SOUTH-B,P-WEST-B)
			ZONE-NAMES			= 	(P-EAST-B,P-SOUTH-B,P-WEST-B,P-INT-B,
						   		EASTROOM-B,SOUTHROOM-B,WESTROOM-B,INTROOM-B) 
			ZONE-HEAT-SOURCE 		= ELECTRIC
			RETURN-AIR-PATH		= PLENUM-ZONES ..

AHU-MAIN	= SYSTEM
			SYSTEM-CONTROL		= SC-MAIN
			SYSTEM-AIR			= SA-MAIN
			SYSTEM-FANS			= SYSTEM-FAN-ALL
			SYSTEM-TERMINAL		= ST-MAIN
			SYSTEM-TYPE			= VAVS
			PLENUM-NAMES		= (P-MED-1,P-COMPUTER,P-OFFICE)
			ZONE-NAMES			= (P-MED-1,P-COMPUTER,P-OFFICE,P-BREAK,P-RECEPTION,
						   	P-CLASS-W,P-CLASS-E,P-DISPLAY,
						   	MEDIA-CENTER,COMPUTER-RM,OFFICE,BREAKROOM,RECEPTION-RM,
						   	CLASSROOM-W,CLASSROOM-E,DISPLAY-RM,MECH-ROOM,STORAGE-RM) 
			ZONE-HEAT-SOURCE 	= ELECTRIC
			RETURN-AIR-PATH		= PLENUM-ZONES ..


$************************** PLANT ASSIGNMENT *************************************************
PLANT-1	= PLANT-ASSIGNMENT
			SYSTEM-NAMES	= (AHU-MAIN,AHU-A,AHU-B) ..


$****************** REPORTS ******************************
$** VERIFICATION AND SUMMARY REPORT **
$SYSTEMS-REPORT	VERIFICATION 	= (SV-A)	
$			SUMMARY	 	= (SS-A,SS-D,SS-L)
$			REPORT-FREQUENCY 	= HOURLY
$			HOURLY-DATA-SAVE 	= FORMATTED ..

$ SV-D = SYSTEM DESIGN PARAMETERS
$ SS-A = SYSTEM MONTHLY LOADS SUMMARY
$ SS-B = PLANT MONTHLY LOADS SUMMARY
$ SS-L = FAN ELECTRIC ENERGY


$** LOAD HOURLY REPORT **
S-REPORT-SCH	= SCHEDULE THRU DEC 31 (ALL) (1,24) VALUES = (1) ..

$* REPORT BLOCK FOR ZONE TEMPERATURE, CFM, AND ZONE COIL HEATING WITH VARIABLE LIST 6,14,32
RS-EA	= R-B	V-T = EASTROOM-A	V-L = ( 6, 14, 32) ..
RS-SA	= R-B	V-T = SOUTHROOM-A	V-L = ( 6, 14, 32) ..
RS-WA	= R-B	V-T = WESTROOM-A	V-L = ( 6, 14, 32) ..
RS-IA	= R-B	V-T = INTROOM-A	V-L = ( 6, 14, 32) ..
RS-EB	= R-B	V-T = EASTROOM-B	V-L = ( 6, 14, 32) ..
RS-SB	= R-B	V-T = SOUTHROOM-B	V-L = ( 6, 14, 32) ..
RS-WB	= R-B	V-T = WESTROOM-B	V-L = ( 6, 14, 32) ..
RS-IB	= R-B	V-T = INTROOM-B	V-L = ( 6, 14, 32) ..  $1,6,14,32
RS-EAL = R-B	V-T = END-USE	V-L = (1) ..

HOURLY-SYSTEMEA	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-EA)
				OPTION		=  PRINT ..

HOURLY-SYSTEMEB	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-EB)
				OPTION		=  PRINT ..

HOURLY-SYSTEMSA	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-SA)
				OPTION		=  PRINT ..

HOURLY-SYSTEMSB	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-SB)
				OPTION		=  PRINT ..

HOURLY-SYSTEMWA	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-WA)
				OPTION		=  PRINT ..

HOURLY-SYSTEMWB	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-WB)
				OPTION		=  PRINT ..

HOURLY-SYSTEMIA	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-IA)
				OPTION		=  PRINT ..

HOURLY-SYSTEMIB	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-IB)
				OPTION		=  PRINT ..

$* REPORT BLOCK FOR AHU CFM,OA RATIO,TOTAL FAN KW,SF-KW,RF-KW,HCOIL-T,CCOIL-T (17,39,33,49,50,1,2)
$RS-AB	= R-B	V-T = AHU-B		V-L = (17,39,33,49,50,1,2) ..

$HOURLY-SYSTEM2	= HOURLY-REPORT
$				REPORT-SCHEDULE	= S-REPORT-SCH
$				REPORT-BLOCK	= (RS-AB)
$				OPTION		= PRINT ..



$* REPORT BLOCK FOR COOLING COIL ENERGY INPUT AND TOTAL ZONE HEATING ENERGY INPUT (6 & 7)
RS-SYA		= R-B	V-T = AHU-A		V-L = (17,39,3,2,4,6) ..
RS-SYB		= R-B	V-T = AHU-B		V-L = (17,39,3,2,4,6) ..

HOURLY-SYSTEM3	= HOURLY-REPORT	
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-SYA)
				OPTION		= PRINT ..
HOURLY-SYSTEM4	= HOURLY-REPORT	
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-SYB)
				OPTION		= PRINT ..
END ..
COMPUTE SYSTEMS ..
STOP ..



