$ Yearly simulation using DOE2 for ERS at Ankeny, Iowa
$ Schedules used are the typical offfice building during a year
$ Room B use daylighting (DAYLIGHTING = YES)
$ Comparison for ERH vs HRH
$ Air flow rate with ERH (250,400 CFM) (450,1000 CFM)
$ Fan is on CYCLE-ON-ANY mode
$ Temperature is controlled

$*********************************************************************************
$                    		INPUT FOR ERS LOAD                                 *
$*********************************************************************************
INPUT LOADS		INPUT-UNITS = ENGLISH	OUTPUT-UNITS = METRIC ..

TITLE			LINE-1 *ERS YEARLY ENERGY SIMULATION* ..

ABORT			IF ERRORS ..

DIAGNOSTIC		WARNINGS	CAUTIONS ..

RUN-PERIOD		JUN 4 2005 THRU JUN 10 2005 ..

$****************************** BUILDING DESCRIPTION *****************************
BUILDING-LOCATION	LATITUDE = 41.71		LONGITUDE = 93.61
			ALTITUDE = 	945		AZIMUTH = 0.0	
			TIME-ZONE = 6		DAYLIGHT-SAVINGS = NO
			HOLIDAY = NO
			GROUND-T = (90,90,90,90,90,66.94,66.74,90,90,90,90,90) ..


$********************** SCHEDULES FOR TEST ROOMS *********************************

$*** EQUIPMENT ********
EQP-SCH-A		= SCHEDULE THRU DEC 31
				(ALL)	(1,24)(1) ..

EQP-SCH-B		= SCHEDULE THRU DEC 31
				(ALL)	(1,24)(1) ..

EQP-SCH			= SCHEDULE THRU DEC 31
				(ALL)	(1,24)(1) ..

$*** LIGHTING *********
LIGHT-SCH		= SCHEDULE THRU DEC 31
				(ALL)	(1,4)(0) (5,21)(1) (22,24)(0)..

$****WINDOW SHADING SCHEDULES
TVIS-NYSAN-SCH     	= 	SCHEDULE THRU DEC 31 (ALL)(1,24)(0.305) ..

TSOL-NYSAN-SCH     	= 	SCHEDULE THRU DEC 31 (ALL)(1,24)(0.304) ..

COND-NYSAN-SCH		=	SCHEDULE THRU DEC 31 (ALL)(1,24)(0.7422) ..

DAYLIGHT-SCH		=	SCHEDULE THRU DEC 31 (ALL)(1,24)(1) ..

TVIS-MUSLIN-SCH     	= 	SCHEDULE THRU DEC 31 (ALL)(1,24)(0.388) ..

TSOL-MUSLIN-SCH     	= 	SCHEDULE THRU DEC 31 (ALL)(1,24)(0.384) ..

COND-MUSLIN-SCH		=	SCHEDULE THRU DEC 31 (ALL)(1,24)(0.7422) ..





$********************** SCHEDULES FOR OTHER ROOMS *********************************
ZERO-SCH		= SCHEDULE THRU DEC 31 (ALL) (1,24)(0) ..
PEOPLE-STANDARD	= SCHEDULE THRU DEC 31 (ALL) (1,7)(0) (8,18)(1) (19,24)(0) ..
LIGHT-STANDARD	= SCHEDULE THRU DEC 31 (ALL) (1,7)(0.05) (8,18)(1) 
							     (19,24)(0.05) ..
EQP-STANDARD	= SCHEDULE THRU DEC 31 (ALL) (1,7)(0) (8,18)(1) (19,24)(0) ..


$***************************** MATERIAL DEFINITION ********************************
$** THIS MATERIAL DEFINITION FOR MATERIAL THAT IS NOT AVAILABLE IN DOE2 DATABASE **
GL1			= MATERIAL
				THICKNESS = 0.0208	CONDUCTIVITY = 0.797
				DENSITY = 138.5		SPECIFIC-HEAT = 0.178 ..

UDCC03		= MATERIAL
				THICKNESS = 0.33333	CONDUCTIVITY = 0.7576
				DENSITY = 140 		SPECIFIC-HEAT = 0.2 ..
PInsulation		= MATERIAL 
				RESISTANCE    = 5 ..   



$***************************** GLASS TYPES ****************************************
LOW-E2 		= GLASS-TYPE
			  GLASS-TYPE-CODE = 2001
			  FRAME-ABS = 0.7
			  FRAME-CONDUCTANCE = 2.77
			  SPACER-TYPE-CODE = 1 ..

LOW-E3	 	= GLASS-TYPE
			  GLASS-TYPE-CODE = 2000
			  FRAME-ABS = 0.7
			  FRAME-CONDUCTANCE = 2.77
			  SPACER-TYPE-CODE = 1 ..

CLEAR	 	= GLASS-TYPE
			  GLASS-TYPE-CODE = 2002
			  FRAME-ABS = 0.7
			  FRAME-CONDUCTANCE = 2.77
			  SPACER-TYPE-CODE = 1 ..

WINDOW-TYPICAL	= GLASS-TYPE
				SHADING-COEF = 0.31	GLASS-CONDUCTANCE = 0.30
				PANES = 2 ..

WINDOW-SKYLITE	= GLASS-TYPE
				SHADING-COEF = 0.35	GLASS-CONDUCTANCE = 0.24
				PANES = 1 ..

$***************************** LAYERS DEFININTION **********************************
SET-DEFAULT FOR LAYERS 		INSIDE-FILM-RES = 0.68 .. $ FOR EXTERIOR WALLS & ROOFS

$** ROOF FOR BUILDING EXCEPT THE CLASS ROOMS **
LAY-ROOF		= LAYERS 	MATERIAL = (RG02,AR02,IN47,BP01,CC02,AL23,CC02) 
					I-F-R = 0.61 ..	

$** ROOF FOR CLASS ROOM **
LAY-CLASS-ROOF	= LAYERS	MATERIAL = (RG02,AR02,IN47,AS01) I-F-R = 0.61 ..

$** BOTTOM WALL FOR TEST ROOMS **
LAY-TESTWALL-B	= LAYERS	MATERIAL = (CC03,IN42,IN43,AL11,BP01,GP02) 
					I-F-R = 0.68 ..

$** TOP WALL FOR TEST ROOMS **
LAY-TESTWALL-T	= LAYERS	MATERIAL = (CC04,IN43,AL11,GP02) I-F-R = 0.68  ..

$** SPANDREL WALL **
LAY-SPAND-WALL	= LAYERS 	MATERIAL = (GL1,AL11,GL1,AL31,IN43,IN13,BP01,GP02) 
					I-F-R = 0.68  ..

$** OVERHEAD WALL **
LAY-OVH-WALL	= LAYERS	MATERIAL = (CC04,IN43,AL11,IN13) I-F-R = 0.68 ..

$** CLASS ROOMS WALL **
LAY-CLASS-WALL	= LAYERS	MATERIAL = (CC04,IN43,AL21,IN13,BP01,GP03) 
					I-F-R = 0.68 ..

$** BOTTOM WALL FOR BUILDING **
LAY-WALL-B		= LAYERS	MATERIAL = (CC03,IN43,AL11,IN13,BP01,GP02) 
					I-F-R = 0.68 ..

$** TOP WALL FOR BUILDING **
LAY-WALL-T		= LAYERS	MATERIAL = (CC03,IN43,AL11,IN13,GP02) 
					I-F-R = 0.68 ..

$** INTERIOR WALL
LAY-INT-WALL	= LAYERS 	MATERIAL = (GP02,IN13,GP02) I-F-R = 0.68 ..

$** CEILING **
LAY-CEILING		= LAYERS 	MATERIAL = (AC03)		I-F-R = 0.92 ..

$** GROUND FLOOR **
LAY-FLOOR		= LAYERS	MATERIAL =  (PInsulation, CC03,CP02)	I-F-R = 0.61 ..


$*** CONSTRUCTIONS DEFINITION FOR ROOF, WALL, CEILING, PARTITION, FLOOR, WINDOW AND DOOR *****

$** ROOF FOR BUILDING EXCEPT CLASS ROOM **
ROOF-STD		= CONSTRUCTION
				LAYERS = LAY-ROOF	
				ABSORPTANCE = 0.29	ROUGHNESS = 1 ..

$** ROOF FOR CLASS ROOM **
ROOF-CLASS		= CONSTRUCTION LIKE ROOF-STD	
				LAYERS = LAY-CLASS-ROOF ..

$** TEST ROOM BOTTOM WALL **
WALL-TESTROOM-B	= CONSTRUCTION
				LAYERS = LAY-TESTWALL-B
				ABSORPTANCE = 0.69	ROUGHNESS = 3 ..

$** TEST ROOM TOP WALL **
WALL-TESTROOM-T	= CONSTRUCTION LIKE WALL-TESTROOM-B		
				LAYERS = LAY-TESTWALL-T ..

$** SPANDRELL WALL **
WALL-SPANDRELL	= CONSTRUCTION
				LAYERS = LAY-SPAND-WALL
				ABSORPTANCE = 0.90	ROUGHNESS = 6 ..

$** OVERHEAD WALL **
WALL-OVERHEAD	= CONSTRUCTION LIKE WALL-TESTROOM-B
				LAYERS = LAY-OVH-WALL ..

$** CLASSROOM WALL **
WALL-CLASSROOM	= CONSTRUCTION LIKE WALL-TESTROOM-B
				LAYERS = LAY-CLASS-WALL ..

$** TYPICAL BUILDING BOTTOM-WALL **
WALL-BOTTOM		= CONSTRUCTION LIKE WALL-TESTROOM-B
				LAYERS = LAY-WALL-B ..

$** TYPICAL BUILDING TOP-WALL **
WALL-TOP		= CONSTRUCTION LIKE WALL-TESTROOM-B
				LAYERS = LAY-WALL-T ..

$** INTERIOR WALL FOR SPACE "INTERIOR-WALL" **
INT-WALL		= CONSTRUCTION		LAYERS = LAY-INT-WALL ..

$** INTERIOR WALL FOR INTERIOR ROOMS
WALL-INT	 	= CONSTRUCTION		U = 0.6 ..

$** CEILING **
CEILING		= CONSTRUCTION		LAYERS = LAY-CEILING ..

$** GROUND FLOOR **
GND-FLOOR		= CONSTRUCTION	 U = 0.140418 ..	$ LAYERS = LAY-FLOOR ..




$******************* SPACE CONDITIONS **********************************
$** SPACE CONDITION FOR TEST ROOM **

TEST-ROOM-A		= SPACE-CONDITIONS
				ZONE-TYPE		= CONDITIONED
				TEMPERATURE		= (72.5)
				LIGHTING-SCHEDULE	= LIGHT-SCH
				LIGHTING-TYPE	= REC-FLUOR-NV 
				LIGHT-TO-SPACE	= 0.8  $ 1
				LIGHTING-KW		= 0.5
				LIGHT-RAD-FRAC	= (0)
				EQUIP-SCHEDULE	= EQP-SCH
				EQUIPMENT-KW	= 1
				FLOOR-WEIGHT	= 0 ..

TEST-ROOM-WA	= SPACE-CONDITIONS
				ZONE-TYPE		= CONDITIONED
				TEMPERATURE		= (71.6)
				LIGHTING-SCHEDULE	= LIGHT-SCH
				LIGHTING-TYPE	= REC-FLUOR-NV 
				LIGHT-TO-SPACE	= 0.18
				LIGHTING-KW		= 0.345
				DAYLIGHTING		= YES
				LIGHT-REF-POINT1	= (9.333,7.335,2.375)
				LIGHT-SET-POINT1	= 60 	
				ZONE-FRACTION1	= 1.0
				LIGHT-CTRL-TYPE1	= CONTINUOUS/OFF
				MIN-LIGHT-FRAC    = 0.046159
				MIN-POWER-FRAC	= 0.25217
				LIGHT-RAD-FRAC	= (0.8)
				FLOOR-WEIGHT	= 0
				EQUIPMENT-KW	= 1.015
				EQUIP-SENSIBLE	= 1
				EQUIP-SCHEDULE	= EQP-SCH-A ..

TEST-ROOM-WB	= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (71.6)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-NV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.353
				DAYLIGHTING			= YES
				LIGHT-REF-POINT1		= (9.333,7.335,2.375) 
				LIGHT-SET-POINT1		= 60 	
				ZONE-FRACTION1		= 1.0
				LIGHT-CTRL-TYPE1		= CONTINUOUS/OFF
				MIN-LIGHT-FRAC    	= 0.041357
				MIN-POWER-FRAC		= 0.24051
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				EQUIPMENT-KW		= 1.015
				EQUIP-SENSIBLE		= 1
				EQUIP-SCHEDULE		= EQP-SCH-B ..

TEST-ROOM-EA	= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (71.6)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-NV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.349
				LIGHT-RAD-FRAC		= (0.8)
				DAYLIGHTING			= YES
				LIGHT-REF-POINT1		= (6.076,7.335,2.375)
				LIGHT-SET-POINT1		= 60 	
				ZONE-FRACTION1		= 1.0
				LIGHT-CTRL-TYPE1		= CONTINUOUS/OFF
				MIN-LIGHT-FRAC    	= 0.03423
				MIN-POWER-FRAC		= 0.2476
				FLOOR-WEIGHT		= 0
				EQUIPMENT-KW		= 1.015
				EQUIP-SENSIBLE		= 1
				EQUIP-SCHEDULE		= EQP-SCH-A ..

TEST-ROOM-EB	= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (71.6)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-NV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.366
				DAYLIGHTING			= YES
				LIGHT-REF-POINT1		= (6.076,7.335,2.375)
				LIGHT-SET-POINT1		= 60 	
				ZONE-FRACTION1		= 1.0
				LIGHT-CTRL-TYPE1		= CONTINUOUS/OFF
				MIN-LIGHT-FRAC    	= 0.04523
				MIN-POWER-FRAC		= 0.24803
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				EQUIPMENT-KW		= 1.015
				EQUIP-SENSIBLE		= 1
				EQUIP-SCHEDULE		= EQP-SCH-B ..

TEST-ROOM-SA	= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (71.6)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-NV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.344
				DAYLIGHTING			= YES
				LIGHT-REF-POINT1		= (7.335,9.333,2.375)
				LIGHT-SET-POINT1		= 60 	
				ZONE-FRACTION1		= 1.0
				LIGHT-CTRL-TYPE1		= CONTINUOUS/OFF
				MIN-LIGHT-FRAC    	= 0.045539
				MIN-POWER-FRAC		= 0.2512
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				EQUIPMENT-KW		= 1.015
				EQUIP-SENSIBLE		= 1
				EQUIP-SCHEDULE		= EQP-SCH-A ..

TEST-ROOM-SB	= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (71.6)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-NV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.361
				DAYLIGHTING			= YES
				LIGHT-REF-POINT1		= (7.335,9.333,2.375)
				LIGHT-SET-POINT1		= 60
				ZONE-FRACTION1		= 1.0
				LIGHT-CTRL-TYPE1		= CONTINUOUS/OFF
				MIN-POWER-FRAC		= 0.2421
				MIN-LIGHT-FRAC    	= 0.04213
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				EQUIPMENT-KW		= 1.015
				EQUIP-SENSIBLE		= 1
				EQUIP-SCHEDULE		= EQP-SCH-B ..

TEST-ROOM-IA		= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (71.6)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-NV   
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.359
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				EQUIPMENT-KW		= 0.89
				EQUIP-SENSIBLE		= 1
				EQUIP-SCHEDULE		= EQP-SCH-A ..

$ SPACE CONDITION FOR B ROOMS WITH DAYLIGHTING
TEST-ROOM-IB		= SPACE-CONDITIONS
				ZONE-TYPE			= CONDITIONED
				TEMPERATURE			= (71.6)
				LIGHTING-SCHEDULE		= LIGHT-SCH
				LIGHTING-TYPE		= REC-FLUOR-NV 
				LIGHT-TO-SPACE		= 0.18
				LIGHTING-KW			= 0.359
				LIGHT-RAD-FRAC		= (0.8)
				FLOOR-WEIGHT		= 0
				EQUIPMENT-KW		= 0.89
				EQUIP-SENSIBLE		= 1
				EQUIP-SCHEDULE		= EQP-SCH-B ..

$** SPACE CONDITION FOR OTHER ROOMS **
PLENUMS		= S-C		ZONE-TYPE = PLENUM	FLOOR-WEIGHT = 0 ..


$*********** SPACE DESCRIPTION OF TEST ROOMS IN ERS ********************

$** DESCRIPTION OF PLENUM IN EAST-A ROOM **
P-EAST-A		= SPACE	
				VOLUME = 1237.8	SPACE-CONDITIONS = PLENUMS
				X = 59.95 Y = 28 Z = 8.5 
				AREA = 226.0475 ..
	PEWL-EAST-A		= EXTERIOR-WALL
					X = 15.4088	Y = 0	Z = 0
					AZ = 90	TILT = 90
					HEIGHT = 5.5	WIDTH = 14.67
					CONSTRUCTION = WALL-TESTROOM-T
					G-R = 0.15 ..
	ROOF-EAST-A		= ROOF 
					CONSTRUCTION = ROOF-STD		
					AZIMUTH = 0	
					TILT = 0	
					G-R = 0 	
					H = 15.4088 W = 14.67 ..
	PIW1-EAST-A		= I-W		
					A = 80.685	
					INT-WALL-TYPE = ADIABATIC
					CONS = WALL-INT 
					AZ = 270
					TILT = 90 	..
	PIW2-EAST-A		= I-W		
					A = 84.7484	
					INT-WALL-TYPE = ADIABATIC
					CONS = WALL-INT
					AZ = 180 
					TILT = 90 	..	

	PIW3-EAST-A		= I-W		
					A = 84.7484	
					N-T = P-EAST-B
					CONS = WALL-INT
					AZ = 0
					TILT = 90 	..
	
	CEIL-EAST-A		= I-W		
					A = 226.0475
					N-T = EASTROOM-A
					AZ = 0	
					TILT = 180
					CONSTRUCTION = CEILING
					INSIDE-VIS-REFL = (0.443,0.443)
					INSIDE-SOL-ABS  = (0.512, 0.512) ..

$** DESCRIPTION OF PLENUM IN SOUTH-A ROOM **
P-SOUTH-A		= SPACE	LIKE P-EAST-A
					AREA = 226.0475
					X = 28 Y = 0 Z = 8.5 ..
	PEWL-SOUTH-A	= EXTERIOR-WALL
					X = 0	Y = 0 Z = 0
					AZ = 180	TILT = 90
					HEIGHT = 5.5	WIDTH = 14.67
					CONSTRUCTION = WALL-TESTROOM-T
					G-R = 0.15 ..
	ROOF-SOUTH-A	= ROOF
					CONSTRUCTION = ROOF-STD		
					AZIMUTH = 0	TILT = 0	G-R = 0 	
					HEIGHT = 14.67	WIDTH = 15.41  ..
	PIW1-SOUTH-A	= I-W		
					A = 80.685	
					INT-WALL-TYPE = ADIABATIC
					CONS = WALL-INT   
					AZ = 0
					TILT = 90 ..
	PIW2-SOUTH-A	= I-W		
					A = 84.748	
					INT-WALL-TYPE = ADIABATIC
					CONS = WALL-INT 
					AZ = 90
					TILT = 90 ..
	PIW3-SOUTH-A	= I-W		
					A = 84.748	
					N-T = P-SOUTH-B
					CONS = WALL-INT
					AZ = 270
					TILT = 90 ..

	CEIL-SOUTH-A	= I-W		
					A = 226.0475	
					N-T = SOUTHROOM-A
					TILT = 180
					CONSTRUCTION = CEILING
					INSIDE-VIS-REFL = (0.443,0.443)
					INSIDE-SOL-ABS  = (0.512, 0.512) ..

$** DESCRIPTION OF PLENUM IN WEST-A ROOM **
P-WEST-A		= SPACE	LIKE P-EAST-A X=0 Y = 42.67 Z = 8.5
					AREA = 226.0475 ..
	PEWL-WEST-A		= EXTERIOR-WALL
					X = 0		Y = 14.67	Z = 0
					AZ = 270	TILT = 90
					HEIGHT = 4.5	WIDTH = 15
					CONSTRUCTION = WALL-TESTROOM-T
					G-R = 0.15 ..
	ROOF-WEST-A		= ROOF
					CONSTRUCTION = ROOF-STD		
					AZIMUTH = 0	TILT = 0	G-R = 0 	
					HEIGHT = 15.4088	WIDTH = 14.67  ..

	PIW1-WEST-A		= I-W		
					A = 80.685  	
					INT-WALL-TYPE = ADIABATIC
					CONS = WALL-INT
					AZ = 90
					TILT = 90 ..
	
	PIW2-WEST-A		= I-W		
					A = 84.748
					INT-WALL-TYPE = ADIABATIC
					CONS = WALL-INT
					AZ = 180
					TILT = 90 ..
	PIW3-WEST-A		= I-W		
					A = 84.748
					CONS = WALL-INT
					AZ = 0
					TILT = 90
					N-T = P-WEST-B ..
	CEIL-WEST-A		= I-W		
					A = 226.0475
					AZ = 180 
					N-T = WESTROOM-A
					TILT = 180	
					CONSTRUCTION = CEILING
					INSIDE-VIS-REFL = (0.443,0.443)
					INSIDE-SOL-ABS  = (0.512, 0.512) ..

$** DESCRIPTION OF PLENUM IN INTERIOR-A ROOM **
P-INT-A		= SPACE	LIKE P-EAST-A 
					AREA = 226.0475
					X = 35 Y = 70 Z = 8.5 ..
	ROOF-INT-A		= ROOF
					CONSTRUCTION = ROOF-STD		
					AZIMUTH = 0	TILT = 0	G-R = 0 	
					X = 0	Y = 0	 Z = 4.5
					HEIGHT = 14.67		WIDTH = 15.4088  ..
	PIW1-INT-A		= I-W		
					A = 80.685	
					INT-WALL-TYPE = ADIABATIC 
					CONS = WALL-INT ..
	PIW2-INT-A		= I-W		
					A = 84.748	
					INT-WALL-TYPE = ADIABATIC 
					CONS = WALL-INT ..
	PIW3-INT-A		= I-W		
					A = 84.748 	
					INT-WALL-TYPE = ADIABATIC 
					CONS = WALL-INT ..
	PIW4-INT-A		= I-W		
					A = 80.685	
					N-T = P-INT-B 
					CONS = WALL-INT	..
	CEIL-INT-A		= I-W		
					A = 226.0475	
					N-T = INTROOM-A 
					TILT = 180	
					CONSTRUCTION = CEILING
					INSIDE-VIS-REFL = (0.443,0.443)
					INSIDE-SOL-ABS  = (0.512, 0.512) ..

$** DESCRIPTION OF EAST-A ROOM **
EASTROOM-A		= SPACE
				VOLUME = 1921.4	SPACE-CONDITIONS = TEST-ROOM-EA 
				AREA = 226.0475
				X = 59.95 Y = 28 Z = 0 ..
	REWL-EAST-A		= EXTERIOR-WALL
				X = 15.4088	Y = 0 Z = 0
				AZ = 90	
				TILT = 90
				HEIGHT = 8.5	WIDTH = 15
				CONSTRUCTION = WALL-TESTROOM-B
				INSIDE-VIS-REFL = 0.836
				INSIDE-SOL-ABS  = 0.112
				G-R = 0.15 ..
	W-1-EAST-A		= WINDOW
				X= 0.67 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH ..

	W-2-EAST-A		= WINDOW
				X= 4.16 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH ..

	W-3-EAST-A		= WINDOW
				X= 7.61 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH ..

	W-4-EAST-A		= WINDOW
				X= 11.06 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH ..

	RIW1-EAST-A		= I-W	
				CONS = WALL-INT 	
				AREA = 124.6950
				AZ = 270
				INT-WALL-TYPE = ADIABATIC	
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS  = (0.212,0.212) ..
	
	RIW2-EAST-A		= I-W	
				CONS = WALL-INT	
				AREA = 130.9748
				AZ = 180	
				NEXT-TO = EASTROOM-B
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS  = (0.212,0.212) ..
	RIW3-EAST-A		= I-W
				CONS = WALL-INT		
				AREA = 130.9748	
				NEXT-TO = EASTROOM-B 
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS  = (0.212,0.212)
				AZ = 0 ..
	
	CEIL-EASTRM-A	= I-W
				CONS = CEILING
				INSIDE-VIS-REFL = (0.443,0.443)
				INSIDE-SOL-ABS  = (0.512, 0.512)
				N-T = P-EAST-A
				TILT = 180
				AREA = 226.0475 ..

	
	FLOOR-EAST-A	= UNDERGROUND-FLOOR	
				H = 14.67	
				W = 15.4088
				INSIDE-VIS-REFL =  0.103
				INSIDE-SOL-ABS  =  0.736
				CONS = GND-FLOOR	 ..

$** DESCRIPTION OF SOUTH-A ROOM **

SOUTHROOM-A		= SPACE
				VOLUME = 1921.4	SPACE-CONDITIONS = TEST-ROOM-SA 
				AREA = 226.0475
				X = 28 Y = 0 Z = 0 ..
	REWL-SOUTH-A	= EXTERIOR-WALL
				X = 0 	
				Y = 0		
				Z = 0
				AZ = 180	
				TILT = 90
				HEIGHT = 8.5	
				WIDTH = 14.67
				CONSTRUCTION = WALL-TESTROOM-B
				INSIDE-VIS-REFL = 0.836
				INSIDE-SOL-ABS  = 0.112
				G-R = 0.15 ..
	W-1-SOUTH-A		= WINDOW
				X= 0.67 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH 
				OH-W	= 4.27
				OH-D	= 2.0
				OH-B	= 0.67
				OH-A  = 0.825
				R-F-A = 0.67
				R-F-H = 5.67
				R-F-D = 2
				R-F-B = 0.67  ..

	W-2-SOUTH-A		= WINDOW
				X= 4.16 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH 
				OH-W	= 3.6
				OH-D	= 2
				OH-B	= 0.67
				OH-A  = 0.158 ..

	W-3-SOUTH-A		= WINDOW
				X= 7.61 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH 
				OH-W	= 3.6
				OH-D	= 2
				OH-B	= 0.67
				OH-A  = 0.158  ..

	W-4-SOUTH-A		= WINDOW
				X= 11.06 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH 
				OH-W	= 4.27
				OH-D	= 2.0
				OH-B	= 0.67
				OH-A  = 0.158
				L-F-A = 0.67
				L-F-H = 5
				L-F-D = 2.0
				L-F-B = -0.67  ..
	RIW1-SOUTH-A	= I-W		
				AREA = 130.9748	
				INT-WALL-TYPE = ADIABATIC	
				CONS = WALL-INT
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS	= (0.212, 0.212)
				AZ = 270 ..
	RIW2-SOUTH-A 	= I-W
				AREA = 124.6950	
				INT-WALL-TYPE = ADIABATIC	
				CONS = WALL-INT
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS	= (0.212, 0.212)
				AZ = 90 ..
	RIW3-SOUTH-A	= I-W		
				AREA = 130.9748	
				CONS = WALL-INT
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS	= (0.212, 0.212)
				AZ = 270
				N-T = SOUTHROOM-B ..				
	FLOOR-SOUTH-A	= UNDERGROUND-FLOOR
				H = 15.4088	
				W = 14.67
				INSIDE-VIS-REFL = 0.103
				INSIDE-SOL-ABS =  0.736
				CONS = GND-FLOOR ..

$** DESCRIPTION OF WEST-A ROOM **
WESTROOM-A		= SPACE
				VOLUME = 1921.4	
				SPACE-CONDITIONS	= TEST-ROOM-WA 
				AREA = 226.0475
				X=0 Y = 28  Z = 0 ..

REWL-WEST-A		= EXTERIOR-WALL
				X = 0		Y = 14.67	Z = 0
				AZ = 270	
				TILT = 90
				HEIGHT = 8.5	WIDTH = 14.67
				CONSTRUCTION = WALL-TESTROOM-B
				INSIDE-VIS-REFL = 0.836
				INSIDE-SOL-ABS  = 0.112
				G-R = 0.15 ..
	W-1-WEST-A		= WINDOW
				X= 0.67 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH ..
				

	W-2-WEST-A		= WINDOW
				X= 4.16 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH ..
				

	W-3-WEST-A		= WINDOW
				X= 7.61 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH ..
				

	W-4-WEST-A		= WINDOW
				X= 11.06 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E3
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-NYSAN-SCH
			  	SOL-TRANS-SCH = TSOL-NYSAN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-NYSAN-SCH ..
				
	RIW1-WEST-A		= I-W		
				CONS = WALL-INT
				AREA = 124.6950
				AZ = 90	
				INT-WALL-TYPE = ADIABATIC
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS	= (0.212, 0.212) ..
	RIW2-WEST-A 	= I-W		
				CONS = WALL-INT
				AREA = 130.9748
				AZ = 180	
				INT-WALL-TYPE = ADIABATIC			
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS	= (0.212, 0.212) ..

	RIW3-WEST-A		= I-W		
				CONS = WALL-INT
				AREA = 130.9748	
				NEXT-TO = WESTROOM-B
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABs  = (0.212, 0.212) ..

	FLOOR-WEST-A	= UNDERGROUND-FLOOR
				CONS = GND-FLOOR	
				INSIDE-VIS-REFL = 0.103
				INSIDE-SOL-ABS  = 0.736 
				H = 14.67	W = 15.4088 	..

$** DESCRIPTION OF INTERIOR-A ROOM **
INTROOM-A		= SPACE
				VOLUME = 1921.4	SPACE-CONDITIONS = TEST-ROOM-IA 
				AREA = 226.0475
				X = 35 Y = 70 Z = 0 ..
	RIW1-INT-A		= I-W		
				AREA = 124.6950
				TILT = 90	
				INT-WALL-TYPE = ADIABATIC
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS	= (0.212, 0.212)
				CONS = WALL-INT ..
	RIW2-INT-A		= I-W		
				AREA = 130.9748
				TILT = 90	
				INT-WALL-TYPE = ADIABATIC
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS	= (0.212, 0.212)
				CONS = WALL-INT ..
	RIW3-INT-A		= I-W
				AREA = 130.9748	
				TILT = 90 
				INT-WALL-TYPE = ADIABATIC
				$ NEXT-TO = INTROOM-B
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS	= (0.212, 0.212)
				CONS = WALL-INT ..
	
	RIW4-INT-A		= I-W		
				AREA = 124.6950
				INT-WALL-TYPE = ADIABATIC
				TILT = 90
				INSIDE-VIS-REFL = (0.836, 0.836)
				INSIDE-SOL-ABS	= (0.212, 0.212)
				CONS = WALL-INT
				 ..
	FLOOR-INT-A		=  UNDERGROUND-FLOOR
				INSIDE-VIS-REFL = 0.103
				INSIDE-SOL-ABS  = 0.736 
				H = 15.4088 W = 14.67
				CONS = GND-FLOOR	 ..
	

$** DESCRIPTION OF PLENUM IN EAST-B ROOM **
P-EAST-B		= SPACE	
				LIKE P-EAST-A
				X = 59.95 Y = 42.67 Z = 8.5 ..
	PEWL-EAST-B		= EXTERIOR-WALL
				LIKE PEWL-EAST-A ..
	ROOF-EAST-B		= ROOF	
				LIKE ROOF-EAST-A  ..
	PIW1-EAST-B		= I-W		
				LIKE PIW1-EAST-A ..
	PIW2-EAST-B		= I-W		
				LIKE PIW2-EAST-A
				AZ = 180 ..
	CEIL-EAST-B		= I-W		
				LIKE CEIL-EAST-A
				N-T = EASTROOM-B ..

$** DESCRIPTION OF PLENUM IN SOUTH-B ROOM **
P-SOUTH-B		= SPACE	LIKE P-EAST-B
					X = 42.67 Y = 0 Z = 8.5 ..
	PEWL-SOUTH-B	= EXTERIOR-WALL
				LIKE PEWL-SOUTH-A ..
	ROOF-SOUTH-B	= ROOF
				LIKE ROOF-SOUTH-A ..
	PIW1-SOUTH-B	= I-W
				LIKE PIW1-SOUTH-A ..
	PIW2-SOUTH-B	= I-W
				LIKE PIW2-SOUTH-A
				AZ = 90 ..
	CEIL-SOUTH-B	= I-W	
				LIKE CEIL-SOUTH-A
				N-T = SOUTHROOM-B ..

$** DESCRIPTION OF PLENUM IN WEST-B ROOM **
P-WEST-B		= SPACE	LIKE P-EAST-B
					X = 0 Y = 28 Z = 8.5 ..
	PEWL-WEST-B		= EXTERIOR-WALL
				LIKE PEWL-WEST-A ..
	ROOF-WEST-B		= ROOF
				LIKE ROOF-WEST-A   ..
	PIW1-WEST-B		= I-W
				LIKE PIW1-WEST-A ..
	PIW2-WEST-B		= I-W		
				LIKE PIW2-WEST-A 
				AZ = 180 ..
	CEIL-WEST-B		= I-W
				LIKE CEIL-WEST-A
				N-T = WESTROOM-B ..

$** DESCRIPTION OF PLENUM IN INTERIOR-B ROOM **
P-INT-B		= SPACE	LIKE P-EAST-B 
				X = 20 Y = 70 Z = 8.5 ..
	ROOF-INT-B		= ROOF
				LIKE ROOF-INT-A ..
	PIW1-INT-B		= I-W		
				LIKE PIW1-INT-A	..
	PIW2-INT-B		= I-W	
				LIKE PIW2-INT-A  ..
	CEIL-INT-B		= I-W	
				LIKE CEIL-INT-A
				NEXT-TO = INTROOM-B ..

$** DESCRIPTION OF EAST-B ROOM **
EASTROOM-B		= SPACE
				LIKE EASTROOM-A 
				S-C = TEST-ROOM-EB
				X = 59.95 Y = 42.67 Z=0 ..
	REWL-EAST-B		= EXTERIOR-WALL
				LIKE REWL-EAST-A ..
	W-1-EAST-B		= WINDOW
				X= 0.49 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH  ..

	W-2-EAST-B		= WINDOW
				X= 3.99 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH  ..

	W-3-EAST-B		= WINDOW
				X= 7.44 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0 $FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH  ..

	W-4-EAST-B		= WINDOW
				X= 10.88 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH  ..

	RIW1-EAST-B		= I-W	
				LIKE RIW1-EAST-A ..
	RIW2-EAST-B		= I-W		
				LIKE RIW2-EAST-A 
				AZ = 180 ..
	FLOOR-EAST-B	= UNDERGROUND-FLOOR
					LIKE FLOOR-EAST-A 	..

$** DESCRIPTION OF SOUTH-B ROOM **
SOUTHROOM-B		= SPACE
				LIKE SOUTHROOM-A
				VOLUME = 2234.5	
				SPACE-CONDITIONS = TEST-ROOM-SB
				X = 42.67 Y = 0 Z = 0 ..
	REWL-SOUTH-B	= EXTERIOR-WALL
				LIKE REWL-SOUTH-A ..
	W-1-SOUTH-B		= WINDOW
				X= 0.49 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH  
				OH-W	= 4.27
				OH-D	= 2.0
				OH-B	= 0.67
				OH-A  = 0.825
				R-F-A = 0.67
				R-F-H = 5.67
				R-F-D = 2
				R-F-B = 0.67 
				 ..
			

	W-2-SOUTH-B		= WINDOW
				X= 3.99 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH  
				OH-W	= 3.6
				OH-D	= 2
				OH-B	= 0.67
				OH-A  = 0.158  ..
				

	W-3-SOUTH-B		= WINDOW
				X= 7.44 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH 
				OH-W	= 3.6
				OH-D	= 2
				OH-B	= 0.67
				OH-A  = 0.158  ..
				
	W-4-SOUTH-B		= WINDOW
				X= 10.88 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH  
				OH-W	= 4.27
				OH-D	= 2.0
				OH-B	= 0.67
				OH-A  = 0.158
				L-F-A = 0.67
				L-F-H = 5
				L-F-D = 2.0
				L-F-B = -0.67 ..

	RIW1-SOUTH-B	= I-W		
				LIKE RIW1-SOUTH-A ..
	RIW2-SOUTH-B	= I-W	
				LIKE RIW2-SOUTH-A
				AZ = 90 ..
	FLOOR-SOUTH-B	= UNDERGROUND-FLOOR
				LIKE FLOOR-SOUTH-A  ..

$** DESCRIPTION OF WEST-B ROOM **
WESTROOM-B		= SPACE
				LIKE WESTROOM-A
				X = 0 Y = 28 Z = 0
				SPACE-CONDITIONS = TEST-ROOM-WB
				 ..
	REWL-WEST-B		= EXTERIOR-WALL
				X = 0		Y = 15	Z = 0
				AZ = 270	
				TILT = 90
				HEIGHT = 8.5	WIDTH = 15
				CONSTRUCTION = WALL-TESTROOM-B
				INSIDE-VIS-REFL = 0.836
				INSIDE-SOL-ABS  = 0.112
				G-R = 0.15 ..
	W-1-WEST-B		= WINDOW
				X= 0.49 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH  ..
				

	W-2-WEST-B		= WINDOW
				X= 3.99 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH  ..
				

	W-3-WEST-B		= WINDOW
				X= 7.44 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH  ..
				

	W-4-WEST-B		= WINDOW
				X= 10.88 Y = 3
				HEIGHT = 4.95  WIDTH = 3.28
				FRAME-WIDTH = 0.1485 
				GLASS-TYPE = LOW-E2
				WIN-SHADE-TYPE = FIXED-INTERIOR
			  	VIS-TRANS-SCH = TVIS-MUSLIN-SCH
			  	SOL-TRANS-SCH = TSOL-MUSLIN-SCH 
				SHADING-SCHEDULE = DAYLIGHT-SCH
				CONDUCT-SCHEDULE = COND-MUSLIN-SCH  ..
				

	RIW1-WEST-B		= I-W		
				LIKE RIW1-WEST-A ..
	RIW2-WEST-B 	= I-W		
				LIKE RIW2-WEST-A
				AZ = 180 ..
	FLOOR-WEST-B	= UNDERGROUND-FLOOR
				LIKE FLOOR-WEST-A	 ..

$** DESCRIPTION OF INTERIOR-B ROOM **
INTROOM-B		= SPACE
			LIKE INTROOM-A
			SPACE-CONDITIONS = TEST-ROOM-IB
			X = 20 Y = 70 Z = 0 ..
	RIW1-INT-B		= I-W		
				LIKE RIW1-INT-A ..
	RIW2-INT-B		= I-W		
				LIKE RIW2-INT-A ..
	RIW3-INT-B		= I-W	
				LIKE RIW3-INT-A ..
	RIW4-INT-B		= I-W	
				LIKE RIW4-INT-A ..
	FLOOR-INT-B		= UNDERGROUND-FLOOR 
				LIKE FLOOR-INT-A  ..



$****************** REPORTS ******************************
$** VERIFICATION AND SUMMARY REPORT **
$LOADS-REPORT	VERIFICATION 	= (LV-D)	
$			SUMMARY	 	= (LS-C)
$			REPORT-FREQUENCY 	= HOURLY
$			HOURLY-DATA-SAVE 	= FORMATTED ..

$ LV-D = DETAILS OF EXTERIOR SURFACE IN THE PROJECT
$ LS-C = BUILDING PEAK LOAD COMPONENTS

$** LOAD HOURLY REPORT **
L-REPORT-SCH	= SCHEDULE THRU DEC 31 (ALL) (1,24) (1) ..

RS	= R-B V-T = GLOBAL	V-L = (4,3,13,14,15,2) ..

$* REPORT BLOCK FOR SPACE ELECTRIC FROM LIGHT WITH VARIABLE LIST 45
RL-EALO	= R-B	V-T = EASTROOM-A	V-L = (44) ..
RL-EBLO	= R-B	V-T = EASTROOM-B	V-L = (44) ..
RL-IALO	= R-B	V-T = INTROOM-A	V-L =  (7, 22) .. $(44) ..
RL-IBLO	= R-B	V-T = INTROOM-B	V-L =  (7, 22) .. $(44) ..
RL-SALO	= R-B	V-T = SOUTHROOM-A	V-L = (44) ..
RL-SBLO	= R-B	V-T = SOUTHROOM-B	V-L = (44) ..
RL-WALO	= R-B	V-T = WESTROOM-A	V-L = (44) ..
RL-WBLO	= R-B	V-T = WESTROOM-B	V-L = (44) ..




HOURLY-LOAD0	= HOURLY-REPORT
			REPORT-SCHEDULE	= L-REPORT-SCH
			REPORT-BLOCK	= (RL-EALO,RL-EBLO,RL-IALO,RL-IBLO,
						   RL-SALO,RL-SBLO,RL-WALO,RL-WBLO)
			OPTION		= PRINT ..

$* REPORT BLOCK FOR SPACE ELECTRIC FROM LIGHT WITH VARIABLE LIST 45
RL-EAL	= R-B	V-T = EASTROOM-A	V-L = (45) ..
RL-EBL	= R-B	V-T = EASTROOM-B	V-L = (45) ..
RL-IAL	= R-B	V-T = INTROOM-A	V-L = (45) ..
RL-IBL	= R-B	V-T = INTROOM-B	V-L = (45) ..
RL-SAL	= R-B	V-T = SOUTHROOM-A	V-L = (45) ..
RL-SBL	= R-B	V-T = SOUTHROOM-B	V-L = (45) ..
RL-WAL	= R-B	V-T = WESTROOM-A	V-L = (45) ..
RL-WBL	= R-B	V-T = WESTROOM-B	V-L = (45) ..




HOURLY-LOAD1	= HOURLY-REPORT
			REPORT-SCHEDULE	= L-REPORT-SCH
			REPORT-BLOCK	= (RL-EAL,RL-EBL,RL-IAL,RL-IBL,
						   RL-SAL,RL-SBL,RL-WAL,RL-WBL)
			OPTION		= PRINT ..

RL-EALX	= R-B	V-T = EASTROOM-A	V-L = (49) ..
RL-EBLX	= R-B	V-T = EASTROOM-B	V-L = (49) ..
RL-IALX	= R-B	V-T = INTROOM-A	V-L = (49) ..
RL-IBLX	= R-B	V-T = INTROOM-B	V-L = (49) ..
RL-SALX	= R-B	V-T = SOUTHROOM-A	V-L = (49) ..
RL-SBLX	= R-B	V-T = SOUTHROOM-B	V-L = (49) ..
RL-WALX	= R-B	V-T = WESTROOM-A	V-L = (49) ..
RL-WBLX	= R-B	V-T = WESTROOM-B	V-L = (49) ..

HOURLY-LOAD2	= HOURLY-REPORT
			REPORT-SCHEDULE	= L-REPORT-SCH
			REPORT-BLOCK	= (RL-EALX,RL-EBLX,RL-IALX,RL-IBLX,
						   RL-SALX,RL-SBLX,RL-WALX,RL-WBLX)
			OPTION		= PRINT ..

WEATHER-LOAD	= HOURLY-REPORT
			REPORT-SCHEDULE	= L-REPORT-SCH
			REPORT-BLOCK	= (RS)
			OPTION		= PRINT ..

END ..
COMPUTE LOADS ..


$*********************************************************************************
$                    	INPUT FOR ERS HVAC SYSTEM                                *
$*********************************************************************************
INPUT SYSTEMS	INPUT-UNITS = METRIC	OUTPUT-UNITS = METRIC ..


$****************** SCHEDULE FOR ZONE TEMPERATURES *****************************
$** HEATING SET POINT **
HEAT-SPT	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) TEMP = (22) ..

$** COOLING SET POINT **
COOL-SPT	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) TEMP = (23) ..

$***************** SCHEDULE FOR SUPPLY FAN **************************************
FAN-SCH	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) VALUES = (1) ..

$**************** SCHEDULE FOR OUTSIDE AIR **************************************
OA-SCH-A 	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) VALUES = (0) ..

OA-SCH-B	=SCHEDULE THRU DEC 31
			(ALL) (1,24) VALUES = (0)  ..

$**************** SCHEDULE FOR SYSTEM CONTROL ***********************************
$** HEATING SCHEDULE **
HEAT-SCH	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) VALUES = (1)  ..

$** COOLING SCHEDULE **
COOL-SCH	= SCHEDULE THRU DEC 31
			(ALL)	(1,24) VALUES = (1)  ..

$********************* ZONE CONTROL **********************************************
ZONE-CTRL	= ZONE-CONTROL
			DESIGN-HEAT-T	= 22
			HEAT-TEMP-SCH	= HEAT-SPT
			DESIGN-COOL-T	= 23
			COOL-TEMP-SCH	= COOL-SPT
			THERMOSTAT-TYPE	= PROPORTIONAL
			THROTTLING-RANGE	= 0.1 ..

$********************* ZONE AIR **************************************************
ZA-TEST		= ZONE-AIR		ASSIGNED-CFM	= 1000 ..
ZA-INT		= ZONE-AIR		ASSIGNED-CFM	= 700 ..



$*********************** ZONES OPERATION ******************************************
$** TEST ROOMS A **
P-EAST-A	= ZONE	ZONE-TYPE	= PLENUM ..
P-SOUTH-A	= ZONE	ZONE-TYPE	= PLENUM ..
P-WEST-A	= ZONE	ZONE-TYPE	= PLENUM ..
P-INT-A		= ZONE	ZONE-TYPE	= PLENUM ..

EASTROOM-A	= ZONE
		ZONE-TYPE		= CONDITIONED
		ZONE-CONTROL	= ZONE-CTRL
		ZONE-AIR		= ZA-TEST
		M-C-R			= 0.8
		TERMINAL-TYPE	= SVAV ..

SOUTHROOM-A	= ZONE 	LIKE EASTROOM-A ..
WESTROOM-A	= ZONE	LIKE EASTROOM-A ..
INTROOM-A	= ZONE	LIKE EASTROOM-A	Z-A = ZA-INT	M-C-R = 0.606796 ..

$** TEST ROOMS B **
P-EAST-B	= ZONE	ZONE-TYPE	= PLENUM ..
P-SOUTH-B	= ZONE	ZONE-TYPE	= PLENUM ..
P-WEST-B	= ZONE	ZONE-TYPE	= PLENUM ..
P-INT-B	= ZONE	ZONE-TYPE	= PLENUM ..

EASTROOM-B	= ZONE	LIKE EASTROOM-A ..
SOUTHROOM-B	= ZONE 	LIKE EASTROOM-A ..
WESTROOM-B	= ZONE	LIKE EASTROOM-A ..
INTROOM-B	= ZONE	LIKE INTROOM-A ..




$********************* SYSTEM CONTROL ********************************************
$** TEST ROOMS SYSTEMS **
SC-TEST	= SYSTEM-CONTROL
			MAX-SUPPLY-T		= 35
			MIN-SUPPLY-T		= 1.7
			HEATING-SCHEDULE		= HEAT-SCH
			COOLING-SCHEDULE		= COOL-SCH 
			COOL-CONTROL		= CONSTANT
			COOL-SET-T			= 14.7 ..
			
$********************* SYSTEM AIR ***********************************************
SA-TEST	= SYSTEM-AIR
			OA-CONTROL		= FIXED
			DUCT-AIR-LOSS	= 0
			MIN-OUTSIDE-AIR	= 0
			DUCT-DELTA-T	= 0.0 ..
SB-TEST	= SYSTEM-AIR
			OA-CONTROL		= FIXED
			DUCT-AIR-LOSS	= 0
			MIN-OUTSIDE-AIR	= 0
			DUCT-DELTA-T	= 0.0 ..


$******************** SYSTEM FAN ****************************************************
SYSTEM-FAN-ALL	= SYSTEM-FANS
			FAN-SCHEDULE		=  FAN-SCH
			FAN-CONTROL 		=  INLET	
			SUPPLY-STATIC		=  25.4
			SUPPLY-DELTA-T		=  0.0
			SUPPLY-KW			=  0.0 ..
			$SUPPLY-EFF			=  0.7 ..


$****************** SYSTEM TERMINAL ************************************************
ST-TEST	= SYSTEM-TERMINAL		REHEAT-DELTA-T = 40 	 ..



$******************** SYSTEMS EQUIPMENT ********************************************
SE-TEST = SYSTEM-EQUIPMENT
			C-CAP = 10000000 ..
$******************** SYSTEMS OPERATION ********************************************
AHU-A		= SYSTEM
			SYSTEM-TYPE			= VAVS
			PLENUM-NAMES		= (P-EAST-A,P-SOUTH-A,P-WEST-A)
			ZONE-NAMES			= (P-EAST-A,P-SOUTH-A,P-WEST-A,P-INT-A,
						   		EASTROOM-A,SOUTHROOM-A,WESTROOM-A,INTROOM-A) 
			ZONE-HEAT-SOURCE 		= ELECTRIC
			RETURN-AIR-PATH		= PLENUM-ZONES
			SYSTEM-CONTROL		= SC-TEST
			SYSTEM-AIR			= SA-TEST
			SYSTEM-EQUIPMENT		= SE-TEST
			SYSTEM-FANS			= SYSTEM-FAN-ALL
			SYSTEM-TERMINAL		= ST-TEST ..

AHU-B		= SYSTEM
			SYSTEM-CONTROL		= SC-TEST
			SYSTEM-AIR			= SB-TEST
			SYSTEM-EQUIPMENT		= SE-TEST
			SYSTEM-FANS			= SYSTEM-FAN-ALL
			SYSTEM-TERMINAL		= ST-TEST
			SYSTEM-TYPE			= VAVS
			PLENUM-NAMES		= 	(P-EAST-B,P-SOUTH-B,P-WEST-B)
			ZONE-NAMES			= 	(P-EAST-B,P-SOUTH-B,P-WEST-B,P-INT-B,
						   		EASTROOM-B,SOUTHROOM-B,WESTROOM-B,INTROOM-B) 
			ZONE-HEAT-SOURCE 		= ELECTRIC
			RETURN-AIR-PATH		= PLENUM-ZONES ..




$************************** PLANT ASSIGNMENT *************************************************
PLANT-1	= PLANT-ASSIGNMENT
			SYSTEM-NAMES	= (AHU-A,AHU-B) ..


$****************** REPORTS ******************************
$** VERIFICATION AND SUMMARY REPORT **
$SYSTEMS-REPORT	VERIFICATION 	= (SV-A)	
$			SUMMARY	 	= (SS-A,SS-D,SS-L)
$			REPORT-FREQUENCY 	= HOURLY
$			HOURLY-DATA-SAVE 	= FORMATTED ..

$ SV-D = SYSTEM DESIGN PARAMETERS
$ SS-A = SYSTEM MONTHLY LOADS SUMMARY
$ SS-B = PLANT MONTHLY LOADS SUMMARY
$ SS-L = FAN ELECTRIC ENERGY


$** LOAD HOURLY REPORT **
S-REPORT-SCH	= SCHEDULE THRU DEC 31 (ALL) (1,24) VALUES = (1) ..

$* REPORT BLOCK FOR ZONE TEMPERATURE, CFM, AND ZONE COIL HEATING WITH VARIABLE LIST 6,14,32
RS-EA	= R-B	V-T = EASTROOM-A	V-L = ( 6, 14, 32) ..
RS-SA	= R-B	V-T = SOUTHROOM-A	V-L = ( 6, 14, 32) ..
RS-WA	= R-B	V-T = WESTROOM-A	V-L = ( 6, 14, 32) ..
RS-IA	= R-B	V-T = INTROOM-A	V-L = ( 6, 14, 32) ..
RS-EB	= R-B	V-T = EASTROOM-B	V-L = ( 6, 14, 32) ..
RS-SB	= R-B	V-T = SOUTHROOM-B	V-L = ( 6, 14, 32) ..
RS-WB	= R-B	V-T = WESTROOM-B	V-L = ( 6, 14, 32) ..
RS-IB	= R-B	V-T = INTROOM-B	V-L = ( 6, 14, 32) ..  $1,6,14,32
RS-EAL = R-B	V-T = END-USE	V-L = (1) ..

HOURLY-SYSTEMEA	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-EA)
				OPTION		=  PRINT ..

HOURLY-SYSTEMEB	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-EB)
				OPTION		=  PRINT ..

HOURLY-SYSTEMSA	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-SA)
				OPTION		=  PRINT ..

HOURLY-SYSTEMSB	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-SB)
				OPTION		=  PRINT ..

HOURLY-SYSTEMWA	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-WA)
				OPTION		=  PRINT ..

HOURLY-SYSTEMWB	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-WB)
				OPTION		=  PRINT ..

HOURLY-SYSTEMIA	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-IA)
				OPTION		=  PRINT ..

HOURLY-SYSTEMIB	= HOURLY-REPORT
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-IB)
				OPTION		=  PRINT ..

$* REPORT BLOCK FOR AHU CFM,OA RATIO,TOTAL FAN KW,SF-KW,RF-KW,HCOIL-T,CCOIL-T (17,39,33,49,50,1,2)
$RS-AB	= R-B	V-T = AHU-B		V-L = (17,39,33,49,50,1,2) ..

$HOURLY-SYSTEM2	= HOURLY-REPORT
$				REPORT-SCHEDULE	= S-REPORT-SCH
$				REPORT-BLOCK	= (RS-AB)
$				OPTION		= PRINT ..



$* REPORT BLOCK FOR COOLING COIL ENERGY INPUT AND TOTAL ZONE HEATING ENERGY INPUT (6 & 7)
RS-SYA		= R-B	V-T = AHU-A		V-L = (17,39,3,2,4,6) ..
RS-SYB		= R-B	V-T = AHU-B		V-L = (17,39,3,2,4,6) ..

HOURLY-SYSTEM3	= HOURLY-REPORT	
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-SYA)
				OPTION		= PRINT ..
HOURLY-SYSTEM4	= HOURLY-REPORT	
				REPORT-SCHEDULE	= S-REPORT-SCH
				REPORT-BLOCK	= (RS-SYB)
				OPTION		= PRINT ..
END ..
COMPUTE SYSTEMS ..
STOP ..



